A liquid hydrogen tank’s rupture disc failed prematurely, which caused the tank to vent its entire gas contents through the tank’s vent stack. Venting was very loud and formed a condensed moisture cloud visible from the top of the stack. Liquid air was also visible coming off the stack. Venting ceased after approximately 5 minutes. On-site staff called the fire department, which arrived promptly and evacuated the area. Normal operations resumed after the Fire Department was able to determine there were no unsafe conditions.
A redundant safety circuit was put into service and the tank returned to normal operation after the failure. Both rupture discs were replaced and the tank was inspected.