The sensing diaphragm of a pressure transducer (PT), as supplied on an outdoor hydrogen compressor, unexpectedly ruptured and released approximately 0.1 kilograms hydrogen to atmosphere from the compressor discharge line. At time of incident, personnel nearby were alerted by a loud 'pop' and dust disturbance. Simultaneously, the facility monitoring system detected loss of the PT signal and initiated equipment shutdown.
A sealed, unclassified electrical control enclosure, part of a listed and certified force-ventilated commercial hydrogen processing unit enclosure, exploded when the equipment manufacturer’s technician pressed the machine stop switch to complete factory commissioning procedure. The technician was forcefully hit by the flying metal panel holding the switch and sustained serious injuries requiring lengthy hospitalization and rehabilitation. Two were hospitalized. Two others were injured. Significant damage to the indoor facility also occurred.
A hydrogen leak originating from a tank within a high-pressure storage unit serving a hydrogen vehicle fueling station resulted in fire and explosion. Emergency responders were on scene within 7 minutes and contained the fire within 3hours. No damage was reported to the separate forecourt H2 dispenser or to other major station components within the station backcourt compound. No personnel injuries resulted directly from the fire and explosion -a nearby vehicle airbag triggered due to the explosion pressure, with minor injuries to the vehicle occupants.
The sensing diaphragm of a pressure transducer (PT), as supplied on an outdoor hydrogen compressor, unexpectedly ruptured and released approximately 0.1 kilograms hydrogen to atmosphere from the compressor discharge line. At time of incident, personnel nearby were alerted by a loud 'pop' and dust disturbance. Simultaneously, the facility monitoring system detected loss of the PT signal and initiated equipment shutdown. Facility personnel then closed isolation hand valves to stop the leak, locked and tagged out the equipment, and restricted the area.
A sulfur deprivation test was conducted in a sealed 250 ml vessel. More hydrogen was generated in this process than was anticipated, and the vessel cracked.
An incident occurred when Ti-doped sodium alanate was exposed to air, apparently resulting in an unstable compound that experienced a rapid exothermic reaction.
A researcher was working with hydrogen storage materials in a laboratory. Several other researchers were working in adjacent laboratories.
A plume of hydrogen gas escaped from the offloading valve of a liquid hydrogen delivery truck while transporting hydrogen to a commercial facility. The plume ignited, resulting in a flash and concussion loud enough to be heard inside the nearby building and to set off the building’s seismic event detectors. A small amount of hydrogen gas continued to escape from the trailer tank and burn until a company specialist arrived to manually shut off a critical valve almost eight hours later.
A fire erupted from a tanker truck delivering liquid hydrogen to a factory. The ignition of leaking vapors created a plume of flames that rose dozens of feet into the air. The flames receded within seconds, leaving the truck with little damage and its driver unharmed.
The truck was off-loading hydrogen into a tank behind the plant when the incident occurred. The plant reported no delays in its production. It uses the hydrogen in various processes.
During preparation of a new hydrogen storage material, ammonia borane (AB) loaded onto mesoporous carbon, an unexpected incident was observed. As with all procedures with new materials the work is conducted on a small scale and in a laboratory fume hood. They followed the procedures that they had used for absorption of ammonia borane onto mesoporous silica without incident.