While filling a sample cylinder with compressed hydrogen gas, a quick-disconnect coupler fitting came loose within a stainless steel laboratory hood, allowing a small purge of the hydrogen gas to escape directly into the hood through ~1/4-inch Tygon tubing. The stainless steel quick-disconnect fitting struck the stainless steel bottom of the laboratory hood and the hydrogen gas caught fire. It is not known what caused the hydrogen gas to catch fire.
While attempting to light the hydrogen flare inside a Metalorganic Chemical Vapor Deposition (MOCVD) system burn box, a small explosion occurred, blowing the back section of the burn box off. Hydrogen flow was shut down immediately, and this MOCVD operation was suspended. Researchers made the determination that this was a minor incident and there were no injuries.
While refilling the hydrogen system after an outage caused by a power failure, the excess flow valve located at the hydrogen tank tripped, but did not go fully shut.
A hydrogen gas detector on the ground floor of a building registered the release of a small amount of hydrogen gas and actuated automatic alarms both at the fire department and in one of its buildings. Additionally, interlocks connected to the gas detector completely shut down the experiment. Upon hearing the alarm, all occupants (about 6) promptly left the building. Fire department personnel are housed in the trailer next to a building and responded within one minute. They tested the atmosphere within the building, reset the gas detector, and secured the alarm at 9:15.
An employee noticed an unusual smell in a fuel cell laboratory. A shunt inside experimental equipment overheated and caused insulation on conductors to burn. Flames were approximately one inch high and very localized. The employee de-energized equipment and blew out the flames. No combustible material was in the vicinity of the experiment. The fire was contained within the fuel cell and resulted in no damage to equipment.
A 2000-psia-rated gas cylinder (nominal size 10"x1 1/2") was being filled with hydrogen to a target pressure of 1500 psia. The cylinder suffered a failure at an indicated pressure of 1500 psia during filling. Investigation of the failure subsequently revealed that a faulty digital readout had allowed the cylinder to be over-pressurized. There were no safety consequences due to the failure and no damage to the facility or equipment. The cylinder was being filled in a test vault that was specially designed for the high-pressure burst testing of pressure vessels and components.
A facility replaced the copper tubing used for hydrogen distribution, with stainless steel tubing. This was done to address a fire protection concern related to the solder on the copper tubing being susceptible to heat, melting, and releasing a flammable gas. The facility maintenance personnel completed the replacement, noted the pressure on the hydrogen bottle, and left the building. When the maintenance person returned on the following day, s/he noticed the pressure on the hydrogen bottle had dropped 500 psi overnight, indicating a leak in the system.
A guest student was weighing out less than 200 mg of sodium hydride. The material reacted with moisture in the air, producing hydrogen. The heat of the reaction ignited the hydrogen on the end of the spatula being used to transfer the material and at the mouth of the bag holding the stock material (approximately 48 to 50 g). The student attempted to smother the flames with a cotton lab coat hanging nearby. He quickly determined that the lab coat was insufficient to smother the flames and entered the adjoining lab to get a fire extinguisher and warn other lab workers in the area.
A facility manager was notified that an authorization basis requirement, associated with roofing contractor work, had not been met. The requirement was that an unused hydrogen gas cylinder adjacent to the building and not connected to a manifold be removed prior to the use of propane tanks for the hot tar portion of the work.
The project manager failed to remove the extra gas bottle as required because he did not recognize from the bottle color and lack of stencil that the bottle contained hydrogen.
A brazing retort in a shop malfunctioned and resulted in an explosion that propelled the retort shell to the roof of the brazing area and then back to the floor. There were no injuries but damage was sustained by the furnace housing and the retort shell.
Administrative personnel were soon on the scene to make a preliminary assessment of the situation. An expert safety team was retained to assist in the investigation of the explosion. The safety team conducted their initial field investigation on the afternoon of the explosion and again on the following day.