An anhydrous hydrogen fluoride (AHF) lecture bottle spontaneously exploded in a laboratory. No one was injured, but the lab was extensively damaged. The lecture bottle had split along its seam. Its cap and valve assembly were located to the immediate left.
Hydrogen was stored in a plant in a 42 ½ ft diameter sphere made of 3/16 inch steel. The sphere was partitioned into two hemispheres by a neoprene diaphragm attached around the equator. Hydrogen was stored under the diaphragm, while the upper hemisphere contained air. An explosion-proof fan was situated in the upper portion of the sphere in order to provide a slight positive pressure on the top of the diaphragm.
A fire occurred in a hydrogen storage facility. The fire was reported by an employee who saw the fire start after he had aligned valves at the hydrogen storage facility in preparation for putting the hydrogen injection system into service. The employee escaped injury because he was wearing fire-retardant protective clothing and was able to quickly scale a 7-foot-high fence enclosing the hydrogen area. The local fire brigade was dispatched and offsite fire fighting assistance was requested.
An industrial heater used to heat a naphtha-hydrogen mixture developed a small leak in one of its finned tubes. The leak resulted in a 2-ft long torch flame, which was eventually noticed by an employee. Upon discovering the fire, the hydrotreater was shut down by cutting off the flow of naphtha and the flow of fuel to the burners in the heater. The hydrogen flow was maintained in order to cool and sweep the reactor during the shutdown operation.
A rupture occurred in a 24-inch gas line in a reformer. The pipe contained hydrogen and carbon monoxide at a pressure of about 400 psi and a temperature of 930 °C. The ruptured section of pipe had a high-temperature alloy steel outer wall, a refractory liner, and a stainless steel inner liner. The refractory lining had been repaired several times before (including three months prior to the incident) because of localized deterioration and hot spots. The repair procedure consisted of cutting a section of pipe, re-pouring the refractory liner, and patch-welding the outer wall.
A large, hydrogen-cooled generator is driven by steam turbines at a power station. During maintenance shutdowns, the hydrogen cooling loop in the generator is purged with carbon dioxide. After CO2 concentrations are measured with a densitometer to verify the complete removal of hydrogen, the generator is purged with air and the maintenance is performed.
Difficulties were experienced with two solenoid-operated globe valves in a charging system. When shut, the valves could not be reopened without securing all charging pumps. During a refueling outage, the two valves were disassembled and examined to determine the cause of the malfunction. It was found that disc guide assembly springs in both valves had undergone complete catastrophic failure. The springs, which initially had 25 coils, were found in sections of only 1-2 coils.
A water treatment plant used an electrolytic process to generate sodium hypochlorite (NaOCl) from sodium chloride (NaCl). The strategy of using liquid sodium hypochlorite for disinfecting water instead of gaseous chlorine (CL2) is popular because the liquid is generally safer and falls under fewer OSHA and EPA standards. The further idea of generating the liquid sodium hypochlorite on an as-needed basis and in limited quantities also has certain obvious safety advantages.
An offgas system mishap involved two explosions occurring within an interval of about 3 ½ hours. The first offgas explosion was reportedly caused by a welding operation on an air line adjacent to a hydrogen sensor line containing off gas. The welding arc initiated a detonation within the offgas piping. The detonation was contained by the piping system but blew out the water seal at the base of the vent stack.The second hydrogen explosion in this incident occurred in the stack base area.
A hydrogen explosion occurred in an Uninterruptible Power Source (UPS) battery room. The explosion blew a 400 ft2 hole in the roof, collapsed numerous walls and ceilings throughout the building, and significantly damaged a large portion of the 50,000 ft2 building. Fortunately, the computer/data center was vacant at the time and there were no injuries.