The sensing diaphragm of a pressure transducer (PT), as supplied on an outdoor hydrogen compressor, unexpectedly ruptured and released approximately 0.1 kilograms hydrogen to atmosphere from the compressor discharge line. At time of incident, personnel nearby were alerted by a loud 'pop' and dust disturbance. Simultaneously, the facility monitoring system detected loss of the PT signal and initiated equipment shutdown.
A hydrogen leak originating from a tank within a high-pressure storage unit serving a hydrogen vehicle fueling station resulted in fire and explosion. Emergency responders were on scene within 7 minutes and contained the fire within 3hours. No damage was reported to the separate forecourt H2 dispenser or to other major station components within the station backcourt compound. No personnel injuries resulted directly from the fire and explosion -a nearby vehicle airbag triggered due to the explosion pressure, with minor injuries to the vehicle occupants.
During a 70-MPa fueling, the fueling hose breakaway separated. The separation occurred without any extraneous forces other than the pressure of the gas internal to the fueling hose. Upon investigation, it was determined the pull force set point was incorrectly adjusted. No further issues or actions.
An operation to increase the pressure within a hydrogen tube-trailer to 6000 psig was in progress when a burst disk failed at approximately 5200 psig and hydrogen was released. A vent line attached to the burst disk was not sufficiently anchored and bent outward violently from the thrust of the release over an approximate 4-inch moment arm, causing considerable damage to the adjacent vent system components. The operation is conducted with personnel present, but fortunately no one was in proximity when the burst disk failed.
Hydrogen Explosion due to Failure of an Incorrectly Sized Spirometallic Gasket at a Refinery Hydrodesulfurization Plant
Overview: A hydrogen leak and explosion occurred due to the installation of an incorrectly sized gasket at the suction line of a hydrogen compressor in a refinery hydrodesulfurization plant. The incorrectly sized gasket was mounted during the startup of the plant in 2001 and had never being inspected nor replaced.
Operators in a powdered metals production facility heard a hissing noise near one of the plant furnaces and determined that it was a gas leak in the trench below the furnaces. The trench carried hydrogen, nitrogen, and cooling water runoff pipes as well as a vent pipe for the furnaces.
A petroleum refinery experienced a catastrophic rupture at one bank of three heat exchangers in a catalytic reformer/naphtha hydrotreater unit because of high temperature hydrogen attack (HTHA). Hydrogen and naphtha at more than 500F were released from the ruptured heat exchanger and ignited, causing an explosion and an intense fire burned for more than three hours.
A distillate dewaxing unit at an oil refinery was undergoing hot hydrogen regeneration of the catalyst when an explosion occurred. Catalyst regeneration is a periodically performed procedure, in which the normal liquid hydrocarbon feed is stopped and a hydrogen-rich gas mixture is fed through the catalyst bed for which the normal operating temperature is raised from 700F to 800F. During the catalyst regeneration process the reactor pressure is increased from normal operating levels just below 600 psig to about 640 psig.