A large, hydrogen-cooled generator is driven by steam turbines at a power station. During maintenance shutdowns, the hydrogen cooling loop in the generator is purged with carbon dioxide. After CO2 concentrations are measured with a densitometer to verify the complete removal of hydrogen, the generator is purged with air and the maintenance is performed.
A faulty modification to a multiple-gas piping manifold allowed mixing of hydrogen and oxygen that resulted in a storage tube explosion. Several employees suffered severe burn injuries from the incident.
At an offsite liquid H2 fill station, a liquid hydrogen trailer hit a gaseous H2 purge shut off valve handle. Tubing attached to the purge valve was bent on both ends but did not leak.
The driver was not sufficiently careful in approaching the liquid H2 system fill point.
A hydrogen explosion occurred in an emergency battery container used to transfer fuel elements. The container had five emergency power batteries. Damage was incurred by the explosion.
The H2 concentration in the container increased because the battery charger had been left on charge. In addition, the container was placed in an un-ventilated airlock. Ignition of the H2-air mixture was believed to be caused by the relays and micro switches activated when the airlock door was opened.
While a hot air dryer was being used to free a coupling in a hydrogen cryostat (an apparatus used to maintain constant low temperatures), a flash fire occurred. The H2 cryostat was being dismantled.
The temperature at the center of the cryostat was sufficiently low to liquefy air. The prescribed requirements for purging and bringing the cryostat to room temperature were circumvented. The H2 - air mixture was formed and ignition was assumed to be a spark from an open filament of the dryer.
SummaryA fire occurred in a battery manufacturing plant that was about to cease operations for the night. The fire caused an estimated $2.4 million in property damage when an electrical source ignited combustible hydrogen vapors.BackgroundThe incident occurred in the forming room, where wet cell batteries were stored for charging on metal racks. The facility had a wet-pipe sprinkler system, but no automatic hydrogen detection equipment.Incident SynopsisAt 11:52 pm, a security guard on patrol noticed a free burning fire in the forming room and notified the fire department.
A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes.
A refinery hydrocracker effluent pipe section ruptured and released a mixture of gases, including hydrogen, which instantly ignited on contact with the air, causing an explosion and a fire. Excessive high temperature, likely in excess of 1400°F (760°C), initiated in one of the reactor beds spread to adjacent beds and raised the temperature and pressure of the effluent piping to the point where it failed. An operator who was checking a field temperature panel at the base of the reactor and trying to diagnose the high-temperature problem was killed.
A fatal accident took place at an onshore processing facility for slop water from the offshore petroleum industry.
Drilling fluids, or mud, are typically oil-water emulsions consisting of base oil (continuous phase), water (dispersed phase), and emulsifying agents. Used drilling mud, or slop, is mud enriched with water and rock cuttings from drilling --- typically 60-80% water, 10-20% emulated base oil, and 10-20% rock cuttings. The used drilling fluids are collected in slop tanks on oil platforms and later shipped to onshore facilities for further processing.
- = No Ignition
- = Explosion
- = Fire
- = No Ignition
- = Explosion
- = Fire