Hydrogen was stored in a plant in a 42 ½ ft diameter sphere made of 3/16 inch steel. The sphere was partitioned into two hemispheres by a neoprene diaphragm attached around the equator. Hydrogen was stored under the diaphragm, while the upper hemisphere contained air. An explosion-proof fan was situated in the upper portion of the sphere in order to provide a slight positive pressure on the top of the diaphragm.
A hydrogen explosion occurred in an Uninterruptible Power Source (UPS) battery room. The explosion blew a 400 ft2 hole in the roof, collapsed numerous walls and ceilings throughout the building, and significantly damaged a large portion of the 50,000 ft2 building. Fortunately, the computer/data center was vacant at the time and there were no injuries.
A gas-phase explosion in a storage tower with semichemical pulp at a paper mill has possibly been caused by combustion of a mixture of hydrogen and air. The hydrogen was formed by microorganisms in the pulp. Ignition may be due to electric sparks in connection with an electric field in the mist above the pulp.
A hydrogen generation plant experienced a fire and significant damage due to a concussive combustion event that started in a high-pressure hydrogen feed pipe.
During start-up operation of a high-temperature, high-pressure plant using hydrogen, hydrogen gas leaked from the flange of a heat exchanger and a fire occurred. The leakage occurred for two reasons:
Insufficient tightening torque control was carried out during hot-bolting and an unbalanced force was generated across the bolts.
A temperature rise was induced across the heat exchanger as a result of a revamping activity, during a turnaround shutdown.
Hydrogen leaked from a 9,000-gallon horizontal liquid hydrogen tank in the rear of a high-intensity lamp manufacturing facility. The facility manager noticed the leak during his normal morning rounds and initiated the plant's emergency response policy, which included calling the local fire department. A large vapor plume (actually condensed moisture in the air) was visible 200 feet above the tank.
An explosion occurred within the hydrogen processing system of a chemical plant that produces sodium chlorate for bleaching pulp and paper. The chemical process utilizes electrolytic cells and is pH-dependent. Hydrogen is produced as a byproduct and is utilized as a fuel.
An isolated vehicle hydrogen tank needed to be de-fueled, but the standard operating procedure could not be followed because the tank was inoperable and had to be manually vented with a special tool. This intentional release of hydrogen was done outside an R&D facility, but it unintentionally activated two sensors on vehicle bay gas detectors (at 20% LFL) in the adjacent indoor facility. Although each person involved in this activity was qualified to perform the work, the circumstances at the time were unusual.