The cap on a full cylinder of hydrogen was difficult to remove. A wrench was applied to turn the cap. When the cap was turned, a part of the wrench contacted the valve and opened it. Since the cap was still on the cylinder, the valve could not be closed. The area was evacuated until the cylinder had emptied.
An explosion occurred at a chemical plant in an analysis room containing various analyzer instruments, including a gas chromatograph supplied with hydrogen. A contract operator was performing work to install a new vent line to a benzene analyzer that was part of a group of CO2 analyzers, but separate and unrelated to the gas chromatograph. During the process of this work, a plant supervisor accompanying the contract operator doing the work had an indication of flammable gas present on a portable detector. This was in conflict with the fixed gas detector in the analysis room that was indicating that no flammable gas was present. As a precaution, the plant supervisor immediately cut off the hydrogen supply and, along with the contract operator, began the normal task of determining if view more
A refinery hydrocracker effluent pipe section ruptured and released a mixture of gases, including hydrogen, which instantly ignited on contact with the air, causing an explosion and a fire. Excessive high temperature, likely in excess of 1400°F (760°C), initiated in one of the reactor beds spread to adjacent beds and raised the temperature and pressure of the effluent piping to the point where it failed. An operator who was checking a field temperature panel at the base of the reactor and trying to diagnose the high-temperature problem was killed. A total of 46 other plant personnel were injured and 13 of these were taken to local hospitals, treated, and released. There were no reported injuries to the public.
Property damage included an 18-inch (46-centimeter) long tear in the view more
A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes. Just after the 4136 kPa (600 psig) startup steam was introduced into the reformer furnace inlet, the control room alarm journal reported an extreme positive pressure spike at the same time a single loud bang was reported by the operations view more
A hydrogen leak occurred at a plant's hydrogen fill station when a vendor's hydrogen fill truck trailer pulled away after filling and caught an improperly stored hydrogen fill line. The driver of the hydrogen truck trailer did not properly stow the hydrogen fill line after filling and failed to verify that the hydrogen fill line was clear of the trailer prior to departure. As the driver pulled away from the fill station, the hydrogen fill line caught on the trailer and subsequently pulled on the hydrogen fill station's ground storage tubes distribution manifold. The force of this pull bent the plant's hydrogen distribution manifold and hydrogen began leaking from a threaded connection and from the hydrogen fill line. The truck trailer driver reported hearing a view more
An explosion occurred within the hydrogen processing system of a chemical plant that produces sodium chlorate for bleaching pulp and paper. The chemical process utilizes electrolytic cells and is pH-dependent. Hydrogen is produced as a byproduct and is utilized as a fuel.
At the time of the incident, the plant was at an abnormal operating level of 25% capacity. A non-routine maintenance operation to repair high-pH liquid piping was in progress. To assist, operations personnel rerouted the high-pH liquid stream to the plant sump. However, in doing this, the liquid eventually made its way back into the electrolytic process by design. Ultimately this created the root cause of the explosive condition in that the pH of the electrolytic process increased faster than the computer- view more
During a refueling event, the operator activated the fueling lever in the wrong sequence. The vehicle filled to proper pressure, but filled faster than normal. Under different circumstances, this could have resulted in overheating of the receiving fuel tank.
One morning a saltwell pump was placed in operation. Operation of this equipment requires that the Standard Hydrogen Monitoring System (SHMS) cabinet be in operation. Later that morning, during the morning surveillance rounds, the Standard Hydrogen Monitoring System (SHMS) cabinet was found not to be in the operational mode.
On the previous day, the night shift saltwell operator assigned to run the saltwell pump had placed the SHMS monitor in operational mode; however, the saltwell system was not started at this time. Shift turnover was conducted and the condition of the SHMS was turned over to the appropriate saltwell operator and shift manager. During the day shift the day shift operator assigned to the complex received approval from the operations engineer to place the SHMS view more
An unplanned shutdown of the hydrogen supply system occurred, affecting the hydrogen furnaces in the plant. The apparent cause was an inadvertent valve closing, which was contrary to the written procedure.
A preventative maintenance activity was being conducted on the hydrogen gas system. Shortly after starting that work, various hydrogen gas users notified the emergency response personnel that the hydrogen supply safety alarms sounded, indicating an interruption of the hydrogen gas supply. As a result, the hydrogen furnaces shut down. This shut down is an automated process which injects an inert gas (nitrogen or argon) to prevent the introduction of oxygen and its mixing with any hydrogen gas. All shut downs functioned as designed. As a precautionary measure, fire protection view more
During development tests, a gaseous H2 test tank was over pressurized and ruptured. The tank dome was destroyed.
The pressure relief valves were set too high. In addition, the tank was not depressurized while being worked on. Safe distances, as required by the procedures for personnel safety, were not followed.