An isolated vehicle hydrogen tank needed to be de-fueled, but the standard operating procedure could not be followed because the tank was inoperable and had to be manually vented with a special tool. This intentional release of hydrogen was done outside an R&D facility, but it unintentionally activated two sensors on vehicle bay gas detectors (at 20% LFL) in the adjacent indoor facility. Although each person involved in this activity was qualified to perform the work, the circumstances at the time were unusual.
An explosion occurred within the hydrogen processing system of a chemical plant that produces sodium chlorate for bleaching pulp and paper. The chemical process utilizes electrolytic cells and is pH-dependent. Hydrogen is produced as a byproduct and is utilized as a fuel.
At the time of the incident, the plant was at an abnormal operating level of 25% capacity. A non-routine maintenance operation to repair high-pH liquid piping was in progress. To assist, operations personnel rerouted the high-pH liquid stream to the plant sump. However, in doing this, the liquid eventually made its way back into the electrolytic process by design. Ultimately this created the root cause of the explosive condition in that the pH of the electrolytic process increased faster than the computer- view more
Hydrogen leaked from a 9,000-gallon horizontal liquid hydrogen tank in the rear of a high-intensity lamp manufacturing facility. The facility manager noticed the leak during his normal morning rounds and initiated the plant's emergency response policy, which included calling the local fire department. A large vapor plume (actually condensed moisture in the air) was visible 200 feet above the tank. The technician for the hydrogen supplier arrived on site, thawed out the ice buildup around the gland nut from which the leak originated using warm water, and tightened the nut, thus ending the problem. The technician verified that the leak originated from packing material around the valve that had come loose because of the recent extreme cold weather.
The fire department view more
The catalyst in a dehydrogenation reactor, which was usually operated under a hydrogen atmosphere, was changed while the reactor was isolated from the peripheral equipment by closing a 20-inch remotely controlled valve. The hydrogen pressure in the peripheral equipment was set at 20 KPaG, and the reactor was opened to the atmosphere. Anticipating some hydrogen leakage, suction from the piping was accomplished with a vacuum device and, nitrogen sealing was performed. When the piping connections were restored after changing the catalyst, flames spouted from the flange clearance and two workers were burned. One cause of the fire was poor management of the catalyst replacement process.
A catalyst exchange was carried out in a dehydrogenation view more
Hydrogen leaked from the outlet piping of a hydrogen heating furnace at a fuel oil desulfurization cracking unit during normal refinery operation. The leaking hydrogen caused a localized fire. Dilution water for cleaning polythionic acid collected in the drain nozzle after a turnaround shutdown. The chlorine concentration in this dilution water was high because its concentration in the industrial water was originally high. The chlorine in the industrial water was concentrated by the high temperature, after the plant was restarted, and stress corrosion cracking occurred. Hydrogen leaked and was ignited by static electricity or heat.
A fire occurred at the fuel oil desulfurization cracking unit of a refinery 257 hours after startup of the plant, view more
During start-up operation of a high-temperature, high-pressure plant using hydrogen, hydrogen gas leaked from the flange of a heat exchanger and a fire occurred. The leakage occurred for two reasons:
Insufficient tightening torque control was carried out during hot-bolting and an unbalanced force was generated across the bolts.
A temperature rise was induced across the heat exchanger as a result of a revamping activity, during a turnaround shutdown.
Hot-bolting: In equipment and piping that operate at high temperatures, as the temperatures rise, the tightening force decreases, thus re-tightening of bolts is necessary. This work is called hot-bolting. The design conditions of the evaporator where the fire occurred were 2.4 MPaG, view more
A hydrogen generation plant experienced a fire and significant damage due to a concussive combustion event that started in a high-pressure hydrogen feed pipe.
A certain hydrogen plant is designed to continuously produce hydrogen at a purity of 99.75% and at a rate of 510 m3 per day. Hydrogen is produced in two banks of cells filled with a strong solution of caustic soda. Current is passed through the cells to produce hydrogen and oxygen. The oxygen is vented directly to the atmosphere, while the hydrogen is piped to the gasholder. The gasholder is a low-pressure storage vessel capable of storing 28 m3 of gas. It is constructed in two parts. The bottom section is a large round tank. The upper section is an inverted tank or bell that is view more
A gas-phase explosion in a storage tower with semichemical pulp at a paper mill has possibly been caused by combustion of a mixture of hydrogen and air. The hydrogen was formed by microorganisms in the pulp. Ignition may be due to electric sparks in connection with an electric field in the mist above the pulp.
A gas-phase explosion took place in a 1,300 m3 storage tower for semichemical pulp at a paper mill. The storage tower was 21 m high and equipped with an agitator at the bottom. By a pumping arrangement, the pulp was circulated from the bottom to the top through external pipes connected with the mill (Fig. 1).
On a given day the production was stopped at a time when the storage tower was loaded with 1,000 m3 pulp at a view more
A hydrogen explosion occurred in an Uninterruptible Power Source (UPS) battery room. The explosion blew a 400 ft2 hole in the roof, collapsed numerous walls and ceilings throughout the building, and significantly damaged a large portion of the 50,000 ft2 building. Fortunately, the computer/data center was vacant at the time and there were no injuries.
The facility was formerly a large computer/data center with a battery room and emergency generators. The company vacated the building and moved out the computer equipment; however the battery back-up system was left behind. The ventilation for the battery room appeared to be tied into a hydrogen monitoring system. The hydrogen sensor was in alarm upon emergency responders arriving at the scene (post-explosion). 911 callers view more
Hydrogen was stored in a plant in a 42 ½ ft diameter sphere made of 3/16 inch steel. The sphere was partitioned into two hemispheres by a neoprene diaphragm attached around the equator. Hydrogen was stored under the diaphragm, while the upper hemisphere contained air. An explosion-proof fan was situated in the upper portion of the sphere in order to provide a slight positive pressure on the top of the diaphragm.
When the plant was shut down for a local holiday, the fan on top of the hydrogen sphere was also stopped. During plant startup two days later, a violent explosion occurred in the sphere. The sphere shell was torn into many sections by the explosion, and some of the sections were propelled as far as 1,200 ft. Some of these sections struck flammable liquid storage tanks view more