An isolated vehicle hydrogen tank needed to be de-fueled, but the standard operating procedure could not be followed because the tank was inoperable and had to be manually vented with a special tool. This intentional release of hydrogen was done outside an R&D facility, but it unintentionally activated two sensors on vehicle bay gas detectors (at 20% LFL) in the adjacent indoor facility. Although each person involved in this activity was qualified to perform the work, the circumstances at the time were unusual.
Hydrogen leaked from a 9,000-gallon horizontal liquid hydrogen tank in the rear of a high-intensity lamp manufacturing facility. The facility manager noticed the leak during his normal morning rounds and initiated the plant's emergency response policy, which included calling the local fire department. A large vapor plume (actually condensed moisture in the air) was visible 200 feet above the tank. The technician for the hydrogen supplier arrived on site, thawed out the ice buildup around the gland nut from which the leak originated using warm water, and tightened the nut, thus ending the problem. The technician verified that the leak originated from packing material around the valve that had come loose because of the recent extreme cold weather.
The fire department view more