A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes. Just after the 4136 kPa (600 psig) startup steam was introduced into the reformer furnace inlet, the control room alarm journal reported an extreme positive pressure spike at the same time a single loud bang was reported by the operations view more
A hydrogen leak occurred at a plant's hydrogen fill station when a vendor's hydrogen fill truck trailer pulled away after filling and caught an improperly stored hydrogen fill line. The driver of the hydrogen truck trailer did not properly stow the hydrogen fill line after filling and failed to verify that the hydrogen fill line was clear of the trailer prior to departure. As the driver pulled away from the fill station, the hydrogen fill line caught on the trailer and subsequently pulled on the hydrogen fill station's ground storage tubes distribution manifold. The force of this pull bent the plant's hydrogen distribution manifold and hydrogen began leaking from a threaded connection and from the hydrogen fill line. The truck trailer driver reported hearing a view more
An explosion occurred within the hydrogen processing system of a chemical plant that produces sodium chlorate for bleaching pulp and paper. The chemical process utilizes electrolytic cells and is pH-dependent. Hydrogen is produced as a byproduct and is utilized as a fuel.
At the time of the incident, the plant was at an abnormal operating level of 25% capacity. A non-routine maintenance operation to repair high-pH liquid piping was in progress. To assist, operations personnel rerouted the high-pH liquid stream to the plant sump. However, in doing this, the liquid eventually made its way back into the electrolytic process by design. Ultimately this created the root cause of the explosive condition in that the pH of the electrolytic process increased faster than the computer- view more
During normal operations, a two-inch flame was discovered emanating from a pinhole leak in a hydrogen line at an aircraft parts manufacturing facility. Hydrogen was not in use by any process in the facility at the time. The flame was discovered by a contractor who was about to start welding on scaffolding about 3-5 feet away. Before starting, the welder searched the immediate area for any signs of fire per his training. When he spotted the flame, he called his supervisor.
An operator tried to put out the fire with a fire extinguisher, which resulted in the flame enlarging by one inch. All employees and contractors were instructed to leave the area, and the EHS team leader called 911 and informed the fire department that there was a hydrogen fire at the facility. She then put an view more
Overview: A pipe end containing fuel oil corroded at the outlet of a heat exchanger on the outlet side of a desulfurization reactor. The corroded pipe end leaked hydrogen gas, which exploded, causing oil to leak from the heat exchanger. The leaking oil developed into an oil fire, and the damage spread. The causes of the pipe end corrosion include the following:
There was a high concentration of corrosive substances in the process injection water.
The concentration of corrosive substances increased due to re-molding the heat exchangers.
The shape of the pipe cap was dead end piping.
Incident: During normal operations at a fuel oil refinery, a pipe end in a desulfurization unit developed a hydrogen leak, which led to an explosion. The pipe end was located on view more
Hydrogen leaked from the outlet piping of a hydrogen heating furnace at a fuel oil desulfurization cracking unit during normal refinery operation. The leaking hydrogen caused a localized fire. Dilution water for cleaning polythionic acid collected in the drain nozzle after a turnaround shutdown. The chlorine concentration in this dilution water was high because its concentration in the industrial water was originally high. The chlorine in the industrial water was concentrated by the high temperature, after the plant was restarted, and stress corrosion cracking occurred. Hydrogen leaked and was ignited by static electricity or heat.
A fire occurred at the fuel oil desulfurization cracking unit of a refinery 257 hours after startup of the plant, view more
A technician was welding a cable suspended over a stainless steel H2 instrument line. During the welding process, two holes were accidentally burned through the hydrogen tubing. The operator heard a hissing sound and closed the valve, but the hydrogen had already ignited and it burned his hand while he was feeling for a leak.
A short during welding caused the pinholes in the tubing containing the gaseous H2.
A bourdon tube ruptured in a pressure gage after 528 hours of operation in a liquid H2 system. The alarm sounded, the system was isolated and then vented.
A faulty modification to a multiple-gas piping manifold allowed mixing of hydrogen and oxygen that resulted in a storage tube explosion. Several employees suffered severe burn injuries from the incident.
An employee, without authorization, fabricated and installed an adapter to connect a hydrogen tube trailer manifold to an oxygen tube trailer manifold at a facility for filling compressed-gas cylinders for a variety of gases, including hydrogen, oxygen, nitrogen, and helium. A subsequent improper purging procedure allowed oxygen gas to flow into a partially filled hydrogen tube on a hydrogen tube trailer. An ignition occurred in the manifold piping system and a combustion front traveled into the hydrogen tube where, after traveling about a view more
A hydrogen generation plant experienced a fire and significant damage due to a concussive combustion event that started in a high-pressure hydrogen feed pipe.
A certain hydrogen plant is designed to continuously produce hydrogen at a purity of 99.75% and at a rate of 510 m3 per day. Hydrogen is produced in two banks of cells filled with a strong solution of caustic soda. Current is passed through the cells to produce hydrogen and oxygen. The oxygen is vented directly to the atmosphere, while the hydrogen is piped to the gasholder. The gasholder is a low-pressure storage vessel capable of storing 28 m3 of gas. It is constructed in two parts. The bottom section is a large round tank. The upper section is an inverted tank or bell that is view more
- = No Ignition
- = Explosion
- = Fire
- = No Ignition
- = Explosion
- = Fire