A H2 air explosion occurred near a H2 compressor, located outside. Gaseous H2 had been released from a vent stack when a relief valve was actuated. The source of ignition was not known, but considerable damage was inflicted onto the system by the ensuing fire and explosion. Following the explosion, the shut-off valves were closed and the system was vented.
Two relief valves were located in the 3,000 psig system downstream of a 5,000/3,000 regulator. The relief valves were sized to handle substantially different flows. (One was designed for another program.) The relief valve was believed to have opened when the pressure setting was being increased from 2,700 to 2,900 psig. The accuracy of the 5,000 psig gauge used to control the dome of the 5 view more