An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.
One man was killed and another severely injured while working with a portable battery power supply.
At a test facility, a water-submersible portable battery power supply was used to power lighting. The battery power supply contained two 12-volt lead-acid automotive batteries, a wiring harness, and switching relays mounted in an air-tight case suitable for submersion in water. The case possessed ½-inch aluminum walls and a 13.8-pound lid. The box had been used periodically over two years.
After charging all night, the battery power supply was moved into place and connected to the lighting. Two technicians started to test the unit. One technician rested his hand on the case lid while the second leaned over the lid and threw the switch to activate view more