Near the end of the process of filling a gaseous hydrogen tube trailer at a liquid hydrogen transfilling station, a safety pressure-relief device (PRD) rupture disc on one of the tube trailer’s ten tubes burst and vented hydrogen gas. The PRD vent tube directed gas to the top of the trailer where the hydrogen vented and ignited, blowing a flame straight up in the air. The operator filling the tube trailer heard a loud explosion from the sudden release of hydrogen gas and saw flames immediately. The operator closed the main fill valve on the tube trailer, stopping the hydrogen fill; however, the ten cylinders on the tube trailer were almost full (2500 psig/173 bar). The tube trailer involved in this incident was one of two tube trailers being filled simultaneously and was second in a view more
An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.
A hydrogen explosion occurred at a plant, damaging a wall adjacent to the hydrogen storage assembly. The investigation revealed that the explosion was the consequence of deficiencies in components integral to the hydrogen storage assembly, and that this assembly belonged to a supplier contracted to provide hydrogen to the plant. The analysis revealed that had the supplier properly installed and maintained this equipment, this incident would have been prevented. By receiving assurance, on an ongoing basis, that the supplier was properly maintaining this equipment, the company could have also reduced the chance of occurrence of this incident.
A hydrogen supplier was awarded a contract in 1990 to supply the plant with hydrogen as well as to provide view more