An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.
A sealed, unclassified electrical control enclosure, part of a listed and certified force-ventilated commercial hydrogen processing unit enclosure, exploded when the equipment manufacturer’s technician pressed the machine stop switch to complete factory commissioning procedure. The technician was forcefully hit by the flying metal panel holding the switch and sustained serious injuries requiring lengthy hospitalization and rehabilitation. Two were hospitalized. Two others were injured. Significant damage to the indoor facility also occurred.
An independent investigation found that drain lines from the external hydrogen vent stack drain trap and the electrical control enclosure cooler/condenser drain were interconnected into a single external sealed floor drain, in a manner not view more