A distillate dewaxing unit at an oil refinery was undergoing hot hydrogen regeneration of the catalyst when an explosion occurred. Catalyst regeneration is a periodically performed procedure, in which the normal liquid hydrocarbon feed is stopped and a hydrogen-rich gas mixture is fed through the catalyst bed for which the normal operating temperature is raised from 700F to 800F. During the catalyst regeneration process the reactor pressure is increased from normal operating levels just below 600 psig to about 640 psig. A pipe failure occurred as a sudden and complete rupture of the 10-inch diameter line at the exit of one of the two reactors. Security video revealed that the release rapidly exapnded and the hot gas mixture ignited shortly after rupture. A shock wave from the resulting view more
A pressure relief device (PRD) valve failed on a high-pressure storage tube at a hydrogen fueling station, causing the release of approximately 300 kilograms of hydrogen gas. The gas ignited at the exit of the vent pipe and burned for 2-1/2 hours until technicians were permitted by the local fire department to enter the station and stop the flow of gas. During this incident the fire department evacuated nearby businesses and an elementary school, closed adjacent streets, and ordered a high school to shelter in place.
There were no injuries and very little property damage. The corrugated roof on an adjacent canopy over a fueling dispenser was slightly singed by the escaping hydrogen flame, causing less than $300 in damage.
The station's operating systems worked as view more
An over-pressurization of two 55-gallon drums of waste phosphoric acid resulted in a material failure of the drum bottoms, releasing the contents of both drums (about 100 gallons) onto the facility floor. The spillage was collected within the sumps that are part of the facility's spill control system. The waste material had been packaged into DOT-specified containers earlier that day and the drums were placed into an assigned storage cell. That evening a staff member heard a noise in the high bay where hazardous wastes are stored. Upon investigating, he discovered the breached drums and spilled material.
The only material released to the environment was hydrogen gas. The maximum concentration of hydrogen released into the facility was 0.035%, well below the lower view more