A rupture disc blew on a 20,000-gallon liquid hydrogen tank, causing the vent stack to exhaust cold gaseous hydrogen. Emergency responders were called to the scene. To stabilize the tank, the remaining hydrogen was removed from the tank except for a small volume in the heel of the tank that could not be removed manually. The tank vacuum was lost. Firemen sprayed the tank with water and directed a stream onto the fire exiting the vent stack. The water was channeled directly into the open vent stack, and the exiting residual hydrogen gas (between -423 F and -402 F) caused the water in the vent stack to freeze. The water freezing caused the vent stack to be sealed off, disabling the only exit for the cold hydrogen gas. After a time, the residual hydrogen gas in the tank warmed up, causing view more
An explosion occurred within the hydrogen processing system of a chemical plant that produces sodium chlorate for bleaching pulp and paper. The chemical process utilizes electrolytic cells and is pH-dependent. Hydrogen is produced as a byproduct and is utilized as a fuel.
At the time of the incident, the plant was at an abnormal operating level of 25% capacity. A non-routine maintenance operation to repair high-pH liquid piping was in progress. To assist, operations personnel rerouted the high-pH liquid stream to the plant sump. However, in doing this, the liquid eventually made its way back into the electrolytic process by design. Ultimately this created the root cause of the explosive condition in that the pH of the electrolytic process increased faster than the computer- view more
A solution of potassium carbonate was being drawn off to an inventory tank for a turnaround/shutdown maintenance activity at a refinery's hydrogen production unit. On the day of the incident, the solution level in the tower wasn't checked as it should have been, which resulted in hydrogen gas flowing back into the tank until the increased pressure caused the tank to explode. The direct cause of the incident was the workers neglecting to check the solution level in the tower. It is not known whether the potential for backflow of hydrogen gas into the inventory tank was understood beforehand or not.
An explosion occurred due to unexpected backflow of hydrogen gas while a solution of potassium carbonate was being drawn off to an view more
During development tests, a gaseous H2 test tank was over pressurized and ruptured. The tank dome was destroyed.
The pressure relief valves were set too high. In addition, the tank was not depressurized while being worked on. Safe distances, as required by the procedures for personnel safety, were not followed.
While transferring liquid H2 from a tanker, the burst disk ruptured at 50 psi. The pressure limit for the operation was 30 psi.
The operator turned on the pressure valve and left it unattended, permitting pressure buildup past the allowed 30 psi.
While disconnecting a liquid H2 fill line from a liquid H2 trailer, liquid H2 escaped, burning a second man who was holding the hose. The man was burned on his hands and on his stomach.
The liquid H2 shut off valve was partially open, but both men assumed it was closed. Prescribed clothing was being worn.
While a hot air dryer was being used to free a coupling in a hydrogen cryostat (an apparatus used to maintain constant low temperatures), a flash fire occurred. The H2 cryostat was being dismantled.
The temperature at the center of the cryostat was sufficiently low to liquefy air. The prescribed requirements for purging and bringing the cryostat to room temperature were circumvented. The H2 - air mixture was formed and ignition was assumed to be a spark from an open filament of the dryer.
A technician was welding a cable suspended over a stainless steel H2 instrument line. During the welding process, two holes were accidentally burned through the hydrogen tubing. The operator heard a hissing sound and closed the valve, but the hydrogen had already ignited and it burned his hand while he was feeling for a leak.
A short during welding caused the pinholes in the tubing containing the gaseous H2.