A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes. Just after the 4136 kPa (600 psig) startup steam was introduced into the reformer furnace inlet, the control room alarm journal reported an extreme positive pressure spike at the same time a single loud bang was reported by the operations view more
A faulty modification to a multiple-gas piping manifold allowed mixing of hydrogen and oxygen that resulted in a storage tube explosion. Several employees suffered severe burn injuries from the incident.
An employee, without authorization, fabricated and installed an adapter to connect a hydrogen tube trailer manifold to an oxygen tube trailer manifold at a facility for filling compressed-gas cylinders for a variety of gases, including hydrogen, oxygen, nitrogen, and helium. A subsequent improper purging procedure allowed oxygen gas to flow into a partially filled hydrogen tube on a hydrogen tube trailer. An ignition occurred in the manifold piping system and a combustion front traveled into the hydrogen tube where, after traveling about a view more
An explosion occurred in a Microbiological Anaerobic Chamber of approximately 2 m3 capacity that contained an explosive mixture of hydrogen and air. A fire followed the explosion, but was rapidly extinguished by staff using fire extinguishers prior to the arrival of fire service personnel. The pressure wave from the explosion blew windows out of the laboratory, with glass hitting a passerby on a path outside and glass shards landing up to 30 m away. Ceiling panels were dislodged in the laboratory and adjacent rooms, and a worker using the apparatus at the time was taken to the hospital by ambulance for burn treatment. The worker subsequently fully recovered. Another worker in the lab at the time required medical observation, but was otherwise unharmed.
Mixtures of inert gases view more
A researcher was working with hydrogen storage materials in a laboratory. Several other researchers were working in adjacent laboratories.
The researcher had prepared a sample of aluminum deuteride, AlD3, by reacting lithium aluminum deuteride and aluminum chloride in diethyl ether. The actual composition/phase of the material synthesized was unknown, but the researcher had attempted to produce the gamma phase of aluminum deuteride. The synthesis steps used to produce the material were complete and the researcher attempted to seal the material in a glass ampoule for offsite shipment and analysis. The sample size was approximately 1 gram.
The ampoule with the sample had previously been placed under vacuum and had been isolated from the atmosphere. The process for sealing view more