A rupture disc blew on a 20,000-gallon liquid hydrogen tank, causing the vent stack to exhaust cold gaseous hydrogen. Emergency responders were called to the scene. To stabilize the tank, the remaining hydrogen was removed from the tank except for a small volume in the heel of the tank that could not be removed manually. The tank vacuum was lost. Firemen sprayed the tank with water and directed a stream onto the fire exiting the vent stack. The water was channeled directly into the open vent stack, and the exiting residual hydrogen gas (between -423 F and -402 F) caused the water in the vent stack to freeze. The water freezing caused the vent stack to be sealed off, disabling the only exit for the cold hydrogen gas. After a time, the residual hydrogen gas in the tank warmed up, causing view more
A researcher was working with hydrogen storage materials in a laboratory. Several other researchers were working in adjacent laboratories.
The researcher had prepared a sample of aluminum deuteride, AlD3, by reacting lithium aluminum deuteride and aluminum chloride in diethyl ether. The actual composition/phase of the material synthesized was unknown, but the researcher had attempted to produce the gamma phase of aluminum deuteride. The synthesis steps used to produce the material were complete and the researcher attempted to seal the material in a glass ampoule for offsite shipment and analysis. The sample size was approximately 1 gram.
The ampoule with the sample had previously been placed under vacuum and had been isolated from the atmosphere. The process for sealing view more