A rupture disc blew on a 20,000-gallon liquid hydrogen tank, causing the vent stack to exhaust cold gaseous hydrogen. Emergency responders were called to the scene. To stabilize the tank, the remaining hydrogen was removed from the tank except for a small volume in the heel of the tank that could not be removed manually. The tank vacuum was lost. Firemen sprayed the tank with water and directed a stream onto the fire exiting the vent stack. The water was channeled directly into the open vent stack, and the exiting residual hydrogen gas (between -423 F and -402 F) caused the water in the vent stack to freeze. The water freezing caused the vent stack to be sealed off, disabling the only exit for the cold hydrogen gas. After a time, the residual hydrogen gas in the tank warmed up, causing view more
Several parties were involved in hydrogen quality sampling when it was discovered that a hose which was being used in the collection process, connecting two sampling components, was not rated for the pressure to which it was being subjected. Upon discovery, the process was stopped, the hose was removed, and an alternate configuration of the equipment was implemented before carrying on the sampling.
During a 70-MPa fueling, the fueling hose breakaway separated. The separation occurred without any extraneous forces other than the pressure of the gas internal to the fueling hose. Upon investigation, it was determined the pull force set point was incorrectly adjusted. No further issues or actions.
A sealed, unclassified electrical control enclosure, part of a listed and certified force-ventilated commercial hydrogen processing unit enclosure, exploded when the equipment manufacturer’s technician pressed the machine stop switch to complete factory commissioning procedure. The technician was forcefully hit by the flying metal panel holding the switch and sustained serious injuries requiring lengthy hospitalization and rehabilitation. Two were hospitalized. Two others were injured. Significant damage to the indoor facility also occurred.
An independent investigation found that drain lines from the external hydrogen vent stack drain trap and the electrical control enclosure cooler/condenser drain were interconnected into a single external sealed floor drain, in a manner not view more