A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes. Just after the 4136 kPa (600 psig) startup steam was introduced into the reformer furnace inlet, the control room alarm journal reported an extreme positive pressure spike at the same time a single loud bang was reported by the operations view more
SummaryA fire occurred in a battery manufacturing plant that was about to cease operations for the night. The fire caused an estimated $2.4 million in property damage when an electrical source ignited combustible hydrogen vapors.BackgroundThe incident occurred in the forming room, where wet cell batteries were stored for charging on metal racks. The facility had a wet-pipe sprinkler system, but no automatic hydrogen detection equipment.Incident SynopsisAt 11:52 pm, a security guard on patrol noticed a free burning fire in the forming room and notified the fire department. It took fire fighters almost three hours to bring the fire under control.Although the facility was equipped with a wet-pipe sprinkler system, the forming room's branch had been disconnected 10 to 15 years before view more
During preparation of a new hydrogen storage material, ammonia borane (AB) loaded onto mesoporous carbon, an unexpected incident was observed. As with all procedures with new materials the work is conducted on a small scale and in a laboratory fume hood. They followed the procedures that they had used for absorption of ammonia borane onto mesoporous silica without incident.
To absorb the solid AB into a scaffold material they dissolve AB in a dry aprotic polar solvent, THF. The saturated solution of AB in THF is added to the mesoporous carbon material in a round bottom flask, stirred for 10 minutes to saturate the mesoporous scaffold with AB and then the solvent is slowly removed under vacuum. At this point the sample is assumed to be prepared and ready for transfer to a sample view more