An offgas system mishap involved two explosions occurring within an interval of about 3 ½ hours. The first offgas explosion was reportedly caused by a welding operation on an air line adjacent to a hydrogen sensor line containing off gas. The welding arc initiated a detonation within the offgas piping. The detonation was contained by the piping system but blew out the water seal at the base of the vent stack.The second hydrogen explosion in this incident occurred in the stack base area. Hydrogen accumulated in the enclosed base area after the water seal had been blown in the first explosion. The stack base metal door was blown off its hinges from the second explosion, and the reinforced concrete stack was also damaged. A plant employee walking by the stack at the time of the explosion view more
A large, hydrogen-cooled generator is driven by steam turbines at a power station. During maintenance shutdowns, the hydrogen cooling loop in the generator is purged with carbon dioxide. After CO2 concentrations are measured with a densitometer to verify the complete removal of hydrogen, the generator is purged with air and the maintenance is performed.
This purging procedure was used prior to the explosion. The CO2 reading was reported to be 100 percent CO2 at the top of the generator. The cooling system was then purged with air and a 1/2 inch pipe in the cooling loop was cut to install some new instrumentation. When the pipe was cut, pressurized gas was emitted at the opening. Workers assumed the gas was either carbon dioxide or air and proceeded with the new instrument view more
A facility representative observed pipe-fitters enter a containment tent around a riser with a tool bag that contained a mixture of steel and copper/beryllium tools. The top flange was loosened using a copper/beryllium socket and a steel torque wrench. When questioned, the pipe-fitters correctly stated that this was allowable for initial loosening and tightening of these bolts. A copper/beryllium ratchet was used to accomplish the bolt removal. The bonded riser was shifted to allow access for the IH technician. The standard hydrogen monitoring system (SHMS) cabinet and local sample showed no hydrogen/flammable gas was present.
While the continuous vapor sample was being taken, the pipe-fitters proceeded to put together the copper/beryllium ratchet and socket with a 10" view more
A technician was welding a cable suspended over a stainless steel H2 instrument line. During the welding process, two holes were accidentally burned through the hydrogen tubing. The operator heard a hissing sound and closed the valve, but the hydrogen had already ignited and it burned his hand while he was feeling for a leak.
A short during welding caused the pinholes in the tubing containing the gaseous H2.
Two scientists were changing hydrogen gas cylinders in an analytical laboratory. They were in the process of removing the cylinder cap from the new cylinder when a loud hissing noise occurred and they quickly realized that the tank was leaking. After making a quick attempt to shut off the tank, which was not possible, they left the lab and notified their supervisor.
After checking that everyone was out of the lab, the supervisor paged all staff in the vicinity to immediately evacuate to the staging area. Facility management and ES&H management were notified about the situation, and they contacted the local fire department to respond to the site in case the venting gas was ignited.
The first responders arrived quickly and spoke with facility management and the site view more