Hydrogen was found to be leaking from a vent line during cryogenic loading operations. The leak was attributed to a cracked weld on a hydrogen vent line that consisted of (1) double wall aluminum piping and (2) slotted spacers between the inner and outer line to provide a hydrogen gas blanket for insulation. The weld that failed was repaired using a "clamshell" over the area of the failed weld in order to support continued operations. A portion of the failed weld was removed for analysis prior to the repair. After operations, the clamshell repair was excised from the non-vacuum-jacketed double wall piping to allow further analysis of the failed weld. It was later replaced with a new half shell piping section.