An explosion occurred at a chemical plant in an analysis room containing various analyzer instruments, including a gas chromatograph supplied with hydrogen. A contract operator was performing work to install a new vent line to a benzene analyzer that was part of a group of CO2 analyzers, but separate and unrelated to the gas chromatograph. During the process of this work, a plant supervisor accompanying the contract operator doing the work had an indication of flammable gas present on a portable detector. This was in conflict with the fixed gas detector in the analysis room that was indicating that no flammable gas was present. As a precaution, the plant supervisor immediately cut off the hydrogen supply and, along with the contract operator, began the normal task of determining if view more
A refinery hydrocracker effluent pipe section ruptured and released a mixture of gases, including hydrogen, which instantly ignited on contact with the air, causing an explosion and a fire. Excessive high temperature, likely in excess of 1400°F (760°C), initiated in one of the reactor beds spread to adjacent beds and raised the temperature and pressure of the effluent piping to the point where it failed. An operator who was checking a field temperature panel at the base of the reactor and trying to diagnose the high-temperature problem was killed. A total of 46 other plant personnel were injured and 13 of these were taken to local hospitals, treated, and released. There were no reported injuries to the public.
Property damage included an 18-inch (46-centimeter) long tear in the view more
A technician was welding a cable suspended over a stainless steel H2 instrument line. During the welding process, two holes were accidentally burned through the hydrogen tubing. The operator heard a hissing sound and closed the valve, but the hydrogen had already ignited and it burned his hand while he was feeling for a leak.
A short during welding caused the pinholes in the tubing containing the gaseous H2.
A facility experienced a major fire in its Resid Hydrotreater Unit (RHU) that caused millions of dollars in property damage. One employee sustained a minor injury during the emergency unit shutdown and there were no fatalities.
The RHU incident investigation determined that an 8-inch diameter carbon steel elbow inadvertently installed in a high-pressure, high-temperature hydrogen line ruptured after operating for only 3 months. The escaping hydrogen gas from the ruptured elbow quickly ignited.
This incident occurred after a maintenance contractor accidentally replaced an alloy steel elbow with a carbon steel elbow during a scheduled heat exchanger overhaul. The alloy steel elbow was resistant to high-temperature hydrogen attack (HTHA), but the carbon steel elbow was not. view more