A five-pound CO2 cylinder being stored in a compressed gas storage cage at a power plant failed catastrophically and became a missile. The cylinder destroyed the storage cage, then struck one of six stationary hydrogen storage cylinders used as emergency make-up for the hydrogen supply system. One of the hydrogen cylinders was broken away from its mounts and moved 10 feet from its original location. The loss of this cylinder severed the manifold tubing, creating a leak path to the atmosphere for the remaining five hydrogen cylinders. The leaking hydrogen gas apparently self-ignited, engulfing the immediate area. The site fire brigade responded and used hose lines from a distance to provide cooling until the hydrogen supply was consumed. The fire was out within seven minutes, and no off view more
The over-pressurization of a laboratory ball mill reactor designed for operation under slightly elevated pressures resulted in a serious injury. The apparatus had been routinely operated under argon and hydrogen pressures of 5-10 atmospheres for nearly two years. The apparatus had not been tested for operation at pressures greater than 10 atm.
A visiting intern, frustrated in attempts to hydrogenate magnesium silicide through ball milling in the previously noted pressure range, attempted to perform the operation at higher pressures. The approximately 70-ml reactor was loaded in a glove box with 0.5 g of magnesium silicide and six milling balls. Upon pressurization to 80 atmospheres, a 270-degree rupture occurred around the perimeter of the reactor. The blow-out of the reactor view more
Hydrogen was stored in a plant in a 42 ½ ft diameter sphere made of 3/16 inch steel. The sphere was partitioned into two hemispheres by a neoprene diaphragm attached around the equator. Hydrogen was stored under the diaphragm, while the upper hemisphere contained air. An explosion-proof fan was situated in the upper portion of the sphere in order to provide a slight positive pressure on the top of the diaphragm.
When the plant was shut down for a local holiday, the fan on top of the hydrogen sphere was also stopped. During plant startup two days later, a violent explosion occurred in the sphere. The sphere shell was torn into many sections by the explosion, and some of the sections were propelled as far as 1,200 ft. Some of these sections struck flammable liquid storage tanks view more
A 30-milliliter (mL) vacuum bulb, equipped with a glass stopcock, containing one gram of pentacarbonyl manganese hydride exploded in a refrigerator. This caused the breakage of three other containers, releasing some contents into the refrigerator. The chemicals did not react. The refrigerator contained numerous reactive and flammable chemicals, mostly in glass containers.
The damaged containers were removed and relocated under a hood. The refrigerator was then examined for other breakage and inventoried. All breakage was cleaned up. The safety coordinator was notified and began an investigation.
The direct cause of the occurrence was the failure of a glass vacuum bulb, which either fractured due to some unforeseen chemical reaction forming hydrogen gas, or was unable to view more
While research staff were working in a lab, a staff member opened the primary valve to a 0.2" (1500 psi) hydrogen gas line connected to a manifold supplying instruments in the lab. Upon opening the valve, the hydrogen gas line failed at a fitting on the switching manifold, releasing a small amount of hydrogen gas. The staff member closed the valve immediately, then inspected the gas line and found the front ferrule (of the compression-style fitting) to be missing. There were no injuries or damage to equipment.
In the follow-on discussion with research staff, it was learned that approximately one month earlier, a similar condition (front ferrule missing from a fitting) was found while performing a modification to a similar manifold. Following a critique, management expressed view more
An incident occurred when Ti-doped sodium alanate was exposed to air, apparently resulting in an unstable compound that experienced a rapid exothermic reaction.
The sample consisted of mechanically milled NaAlH4 with 4% TiCl3 dopant which was prepared in an argon atmosphere. The sample was sealed and placed in the probe head of an NMR magic angle-spinning (MAS) rotor and spun at approximately 9,000-13,000 rpm. During the process, the sealing cap dislodged and exposed the sample to ambient air for a little less than 24 hours. When discovered, the sample was visually inspected and showed no evidence of oxidation. The sample was re-capped and returned to an argon environment for removal. Most of the sample material was removed using a small stainless steel needle, but a residual view more
A sulfur deprivation test was conducted in a sealed 250 ml vessel. More hydrogen was generated in this process than was anticipated, and the vessel cracked.