A hydrogen leak at the flange of a 6-inch synthesis turbocharger valve in an ammonia production plant ignited and exploded. Hydrogen detectors and the fire alarm alerted the control room, which immediately shut down the plant, and the fire was then extinguished rapidly. There were no injuries caused by the accident, since the operator heard a wheezing sound and was able to run away just before the explosion occurred. The leaking gas was composed of 70% hydrogen at a flow rate of 15,000 cubic meters per hour. Property damages in the turbocharger included electrical cabling, melted siding, and heavily damaged pipes. The ammonia plant was shut down for more than a month.Five days before the incident, a problem with the CO2 absorber column led operators to open the vent downstream of the view more
Severe vibrations caused by broken low-pressure turbine blades damaged the main turbine generator at a nuclear power plant. These vibrations also caused multiple hydrogen leaks at equipment connections to the generator, resulting in hydrogen flames outside of the generator casing that caused minimal damage to the facility. Hydrogen is used to internally cool the plant's electric generators. Water from the fire suppression system and oil released from the turbine lube oil system during the event were contained within the plant, resulting in no impact to the environment. The plant's nuclear systems were unaffected by the event.
A hydrogen leak and subsequent explosion occurred when tie-downs on a hydrogen transport trailer securing hydrogen cylinder packages failed. The tie-down failure caused the hydrogen cylinder packages to fall off the trailer and eject some cylinders onto the roadway (see Figure 1). The cause of the accident is unknown, but it appears to be unrelated to hydrogen (i.e., likely tie-down strap weakness or error in properly securing tie-downs). The cylinders contained compressed hydrogen gas at 200 bar (2900 psi). The accident caused some hydrogen cylinders to leak and the associated cylinder package plumbing systems were breached. A spark or other local heat source (e.g., from a nearby vehicle motor) ignited the leaking hydrogen and caused a deflagration/explosion that damaged a car view more
A sidewall burst failure of a high-pressure polytetrafluoroethylene-lined hose was experienced. The 4.0-m hose was in service for approximately two years, primarily for 70 MPa fueling of hydrogen at ambient conditions ranging from -40 C to +50 C. The total number of fills during its service life was estimated to be 150. In addition to the high-volume fill events, pressure cycling occurred as part of the routine test procedures and operational protocols. These additional pressure-cycling occurrences were approximated to be 200-250 cycles. During each filling cycle, the hose was allowed to bend during connections, as required by the situation. Failure of the hose occurred while temporarily connected to a gas booster, after 1-2 hours of service at 75 MPa. There were no tight bends in the view more