Severe vibrations caused by broken low-pressure turbine blades damaged the main turbine generator at a nuclear power plant. These vibrations also caused multiple hydrogen leaks at equipment connections to the generator, resulting in hydrogen flames outside of the generator casing that caused minimal damage to the facility. Hydrogen is used to internally cool the plant's electric generators. Water from the fire suppression system and oil released from the turbine lube oil system during the event were contained within the plant, resulting in no impact to the environment. The plant's nuclear systems were unaffected by the event.