A hose clamp failed on a low-pressure vent line from a hydrogen reactor experiment and effluent was leaked into the laboratory. Unburnt hydrogen in the effluent stream triggered the low-level hydrogen alarm. The hose clamp was resecured and other hose clamps were checked for proper tightness.
An employee at a soap manufacturing plant died in a flash fire outside the facility's hydrogenation building. Responding personnel encountered a fire at the base of the plant's hydrogen storage towers, and they found the victim, who was burned over 90 percent of his body, some 50 feet away.
Officials determined that a pipe connection failed and that hydrogen, pressurized at 1,800 psi, ignited when it was released into the atmosphere, killing the plant operator.
According to reports, the pipe connection failure stemmed from pressures higher than design tolerance, which in turn were the result of over tightening that occurred during routine maintenance replacement. The new bolts were stronger than those they replaced, and the threads of the nuts had been partially view more