A leaking liquid hydrogen cryogenic pump shaft during the process of filling a gaseous tube delivery trailer to 2400 psi at a liquid hydrogen transfilling location caused a series of explosions and a fire. After approximately 30 minutes of filling, the operator heard a single loud explosion and then saw flames and ripples from heat generation near the ground in the hydrogen fill area. The operator quickly actuated the emergency alarm system that shut down the cryogenic pump and closed the air-actuated valves on the cryogenic pump supply line. After this shutdown, three smaller explosions were heard as well as the sound of gas releasing from a safety relief valve. The fire department was called to the scene and participated in the final shutdown of the hydrogen system as the fire was view more
While performing hydrogen gas release experimentation by thermally reacting a slurry of ammonia borane powder in silicone oil in a plug flow reactor, a discharge port on the test reactor became loose. A foaming white product was leaking from the fitting and discharging in the direction of the heat tape and insulation (back over the reactor). As a result, hot, reacting slurry flowed out of the port and was exposed to air. In the presence of oxygen, the slurry ignited, producing a green flame. A small green flame was noticed at the leak site and flaming product dripped onto the hood deck surface. The flame at the end of the reactor was ~10-12 inches tall at the highest point. The flame on the deck was ~4-6 inches in height.
The incident occurred behind the lowered sashes in the view more