An incident involved an explosion of an oven that was heating decaborane for vaporization. In this incident, the heater controller was defective so the heating element was disconnected from the controller and plugged directly into a wall outlet. This situation allowed the oven to reach temperatures in excess of 400 °C within 20 minutes. While the temperature increased, the decaborane continued to expand, causing a significant pressure build-up within the oven. The pressure increase eventually caused the oven's viewing window to burst. A burst of burning hydrogen was emitted from the window and burned the face of a researcher who was hospitalized for approximately three weeks.
A facility experienced a major fire in its Resid Hydrotreater Unit (RHU) that caused millions of dollars in property damage. One employee sustained a minor injury during the emergency unit shutdown and there were no fatalities.
The RHU incident investigation determined that an 8-inch diameter carbon steel elbow inadvertently installed in a high-pressure, high-temperature hydrogen line ruptured after operating for only 3 months. The escaping hydrogen gas from the ruptured elbow quickly ignited.
This incident occurred after a maintenance contractor accidentally replaced an alloy steel elbow with a carbon steel elbow during a scheduled heat exchanger overhaul. The alloy steel elbow was resistant to high-temperature hydrogen attack (HTHA), but the carbon steel elbow was not. view more
The interior of a small high-temperature furnace, approximately 24 inches high by 18 inches wide, became contaminated with an unknown material later identified as magnesium. The furnace was disassembled to clean the unknown material from the interior surfaces, and while attempting to clean the bottom of the furnace, the technician tapped the upper lip of the furnace with a spatula and the magnesium flashed. The technician was stepping back from the furnace when the magnesium flashed. He received minor eye irritation and his eyebrows were singed.
Later that week the same technician was attempting to clean the interior surfaces of the top of the furnace and sprayed, as directed, the interior of the top with a water-based cleaning liquid which consisted of 91% water. He stepped view more
The catalyst in a dehydrogenation reactor, which was usually operated under a hydrogen atmosphere, was changed while the reactor was isolated from the peripheral equipment by closing a 20-inch remotely controlled valve. The hydrogen pressure in the peripheral equipment was set at 20 KPaG, and the reactor was opened to the atmosphere. Anticipating some hydrogen leakage, suction from the piping was accomplished with a vacuum device and, nitrogen sealing was performed. When the piping connections were restored after changing the catalyst, flames spouted from the flange clearance and two workers were burned. One cause of the fire was poor management of the catalyst replacement process.
A catalyst exchange was carried out in a dehydrogenation view more
A laboratory technician died and three others were injured when hydrogen gas being used in experiments leaked and ignited a flash fire.
The incident occurred in a 5,700-square-foot, single-story building of unprotected non-combustible construction. The building was not equipped with automatic gas detection or fire suppression systems.
Employees in the laboratory were conducting high-pressure, high-temperature experiments with animal and vegetable oils in a catalytic cracker under a gas blanket. They were using a liquefied petroleum gas burner to supply heat in the process.
Investigators believe that a large volume of hydrogen leaked into the room through a pump seal or a pipe union, spread throughout the laboratory, and ignited after coming into contact with the view more
During transfer of liquid H2 from a commercial tank trailer to a receiving vessel, a leak developed in a bayonet fitting at the trailer/facility connection. The leak produced liquid H2 spray which enveloped the rear of the truck where the hand-operated shutoff valve was located. Emergency trained personnel, wearing protective clothing, except for proper shoes, entered the area and shut off the flow control valve. Reentry personnel suffered frost bite of their feet when shoes became frozen to the water-wetted rear deck of the truck.
A loose hose flange connection allowed leakage of cold fluid through the lubricated bayonet seal. This allowed cold fluid to contact and shrink the 'O' ring seal (made of Buna-N rubber), thus permitting view more
A technician was welding a cable suspended over a stainless steel H2 instrument line. During the welding process, two holes were accidentally burned through the hydrogen tubing. The operator heard a hissing sound and closed the valve, but the hydrogen had already ignited and it burned his hand while he was feeling for a leak.
A short during welding caused the pinholes in the tubing containing the gaseous H2.
On a given day personnel were removing a blind hub that had been used to temporarily isolate a portion of a gaseous hydrogen system. As a result of a sudden release of 2,800 psig gaseous nitrogen, sand and debris kicked up from the concrete pad and caused minor injury to two technicians.
During the investigation, it was found that:
The temporary configuration change to the gaseous hydrogen system was initiated on multiple work orders and by different individuals. There was no single document that documented the temporary system configuration.
The procedure for performing the work was written using a drawing that had not been updated to show the actual system configuration. Verbal field direction was given when it was discovered the system was not configured per view more
A hydrogen explosion occurred in a university biochemistry laboratory. Four persons were taken to the hospital for injuries. Three of these were treated and released shortly thereafter; the fourth was kept overnight and released the following evening. All of the exterior windows in the laboratory were blown out and there was significant damage within the laboratory. One sprinkler was activated that controlled a fire associated with a compressed hydrogen gas cylinder.
First responders from the local community and the university campus were quickly on the scene. Once the injured were attended to and the site secured, response efforts focused first on assessing potential hazards (electrical, fire, hazardous materials, etc). Campus personnel worked into the night to board up windows view more