Hydrogen alarms went off in a research laboratory and the fire department was called, but no hydrogen leak was detected. The hydrogen system was leak-checked with helium and found to be leak-free except for a very small leak in the manifold area. The manifold leak was fixed, but because of its small size, it was not thought to be the likely source for the hydrogen alarm trigger. While hydrogen was removed from the system for leak-testing, the hydrogen alarm went off again, and again the fire department responded. There was no hydrogen present in the system to trigger this alarm. Other sources within the building were checked to see what may have set off the alarm, but none were found. One research area uses small amounts of hydrogen, but laboratory logs indicate that none was being view more
A small research sample of approximately 5 grams of aluminum hydride (alane) doped with 2-3 mol % TiCl3 contained within a glass ampoule ruptured after transit while stored in an office cabinet. The rupture was attributed to over-pressurization caused by hydrogen gas buildup within the sample over a four-month period. The glass ampoule, contained within a 0.2-inch thick cardboard shipping tube, was not a pressure-rated container. The rupture resulted in glass chards penetrating the protective cardboard shipping tube. The aluminum hydride, a fine powder, was released from the shipping tube during the pressure release. The fine aluminum powder leaked from the cabinet and set off a local smoke alarm that brought emergency responders to the scene. No personnel were present in the area when view more
During a refueling event, the operator activated the fueling lever in the wrong sequence. The vehicle filled to proper pressure, but filled faster than normal. Under different circumstances, this could have resulted in overheating of the receiving fuel tank.