A student cleaned catalyst that was being used for a fuel cell membrane electrode assembly from a spatula. He then placed the contaminated paper towel into a waste container that contained other waste that was wet with alcohol. The alcohol reacted with the catalyst, igniting a fire within the waste container. The fire was extinguished with a beaker of water.
Installation of a 9000-gallon liquid hydrogen storage tank by a lessee at a building has not been evaluated for effect on the Safety Authorization Basis (SAB) of nearby facilities.
During review of an Emergency Management Hazard Assessment document, a reviewer questioned whether the SAB of nearby facilities had been reviewed for the effect of the installed 9000-gallon liquid hydrogen tank. Reviews by the facility management and facility safety personnel confirmed the evaluations have not been performed.
The direct cause was determined to be a management problem, with policy not adequately defined, disseminated, or enforced to integrate potential lessee hazards into the facility safety program documentation on the 9000-gallon hydrogen tank and delivery. The existing policy view more