A hydrogen explosion occurred in a university biochemistry laboratory. Four persons were taken to the hospital for injuries. Three of these were treated and released shortly thereafter; the fourth was kept overnight and released the following evening. All of the exterior windows in the laboratory were blown out and there was significant damage within the laboratory. One sprinkler was activated that controlled a fire associated with a compressed hydrogen gas cylinder.
Only 25 minutes after the normal work shift ended, an explosion occurred at a hydrogen storage and use facility that had been in a non-operational mode for several months while undergoing modifications for future tests. No one was in the facility at the time of the explosion. The event was viewed about 30 seconds after the explosion by two engineers in a blockhouse 1000 feet away. Authorities were notified and calls were placed to other personnel needed to secure the area. About 8 minutes later, the engineers moved to a vantage point about 450 feet from the facility.
A hydrogen explosion and fire occurred in the benzene unit of a styrene plant in a large petrochemical complex. The unit was being restarted following a scheduled maintenance shutdown. The explosion followed the release of about 30 kilograms of 700-psig hydrogen gas from a burst flange into a compressor shed. Two men were killed and two others were injured. If it had not been a holiday, the death toll and injuries would probably have been much worse.
Hydrogen Explosion due to Failure of an Incorrectly Sized Spirometallic Gasket at a Refinery Hydrodesulfurization Plant
Overview: A hydrogen leak and explosion occurred due to the installation of an incorrectly sized gasket at the suction line of a hydrogen compressor in a refinery hydrodesulfurization plant. The incorrectly sized gasket was mounted during the startup of the plant in 2001 and had never being inspected nor replaced.