A hydrogen explosion and fire occurred in the benzene unit of a styrene plant in a large petrochemical complex. The unit was being restarted following a scheduled maintenance shutdown. The explosion followed the release of about 30 kilograms of 700-psig hydrogen gas from a burst flange into a compressor shed. Two men were killed and two others were injured. If it had not been a holiday, the death toll and injuries would probably have been much worse.
An explosion occurred in a 90-ton-per-day incinerator at a municipal refuse incineration facility. Three workers were seriously burned by high-temperature gas that spouted from the inspection door, and one of them died 10 days later. The accident happened during inspection and repair of the furnace ash chute damper. The workers injected water to remove some blockage, and the water reacted with incinerated aluminum ash to form hydrogen, which caused the explosion.
Hydrogen Explosion due to Failure of an Incorrectly Sized Spirometallic Gasket at a Refinery Hydrodesulfurization Plant
Overview: A hydrogen leak and explosion occurred due to the installation of an incorrectly sized gasket at the suction line of a hydrogen compressor in a refinery hydrodesulfurization plant. The incorrectly sized gasket was mounted during the startup of the plant in 2001 and had never being inspected nor replaced.
Operators in a powdered metals production facility heard a hissing noise near one of the plant furnaces and determined that it was a gas leak in the trench below the furnaces. The trench carried hydrogen, nitrogen, and cooling water runoff pipes as well as a vent pipe for the furnaces.
A petroleum refinery experienced a catastrophic rupture at one bank of three heat exchangers in a catalytic reformer/naphtha hydrotreater unit because of high temperature hydrogen attack (HTHA). Hydrogen and naphtha at more than 500F were released from the ruptured heat exchanger and ignited, causing an explosion and an intense fire burned for more than three hours.