Which ASME B31 piping code should be used for repair and alteration of hydrogen piping systems?
The code used for repair and alterations of an existing system depends on the code used forconstructionas well as on the requirements imposed by the jurisdiction.Note that getting a permit from the jurisdiction may be necessary for an extensive alteration.
|Code of Construction||Generally Accepted Code for Repair and Alterations|
|ASME B31.1||ASME B31.1, Nonmandatory Appendix V Recommended Practice for Operation, Maintenance, and Modification of Power Piping Systems|
|ASME B31.3||API 570 Piping Inspection Code: In-Service Inspection, Rating, Repair and Alteration of Piping Systems|
|ASME B31.12||ASME B31.12, Chapter GR-5 Operation and Maintenance|
|Other Code||Unless otherwise specified, the same as requirements for new construction.|
Note that getting a permit from the jurisdiction may be necessary for an extensive alteration.