A fire occurred in a hydrogen storage facility. The fire was reported by an employee who saw the fire start after he had aligned valves at the hydrogen storage facility in preparation for putting the hydrogen injection system into service. The employee escaped injury because he was wearing fire-retardant protective clothing and was able to quickly scale a 7-foot-high fence enclosing the hydrogen area. The local fire brigade was dispatched and offsite fire fighting assistance was requested. Upon reaching the scene, the local fire department reported seeing a large hydrogen-fueled fire in the vicinity of the hydrogen tube trailer unit. The heat of the fire potentially endangered the nearby hydrogen storage tanks. The onsite fire department, with offsite fire fighting support, fought the view more
While refilling the hydrogen system after an outage caused by a power failure, the excess flow valve located at the hydrogen tank tripped, but did not go fully shut.
The large valve is equipped with a small bypass valve so that the valve can be pressurized on both sides as is required before the valve can be reset. The O-ring which makes this small valve gas tight was deformed and improperly seated, thus allowing gas to flow to each side of the large valve. This permitted the valve to trip normally, but not to seat properly. The following is the manufacturer's evaluation after disassembly and inspection of the valve.
This valve was recently installed to provide excess flow protection to the underground portion of the hydrogen system piping and to provide redundant view more