A pressure relief device (frangible burst disk) on one of a hydrogen delivery tube trailer's 26 tubes failed prematurely and released hydrogen while filling a hydrogen storage tank at a government facility (see Attachment 1). Prior to the filling process, all procedures and safety checks, including connection to the facility's regulator/distribution control system with leak checking and follow-up verification of leak checking by facility personnel, were completed (see Attachment 2 for more details). During the filling process, a person walking near the facility heard the noise of escaping gas that included occasional popping sounds typical of bursts of gas release. Facility personnel were alerted and the tube trailer vendor's incident response team was dispatched to the view more
Near the end of the process of filling a gaseous hydrogen tube trailer at a liquid hydrogen transfilling station, a safety pressure-relief device (PRD) rupture disc on one of the tube trailer’s ten tubes burst and vented hydrogen gas. The PRD vent tube directed gas to the top of the trailer where the hydrogen vented and ignited, blowing a flame straight up in the air. The operator filling the tube trailer heard a loud explosion from the sudden release of hydrogen gas and saw flames immediately. The operator closed the main fill valve on the tube trailer, stopping the hydrogen fill; however, the ten cylinders on the tube trailer were almost full (2500 psig/173 bar). The tube trailer involved in this incident was one of two tube trailers being filled simultaneously and was second in a view more
A hydrogen leak and subsequent explosion occurred when tie-downs on a hydrogen transport trailer securing hydrogen cylinder packages failed. The tie-down failure caused the hydrogen cylinder packages to fall off the trailer and eject some cylinders onto the roadway (see Figure 1). The cause of the accident is unknown, but it appears to be unrelated to hydrogen (i.e., likely tie-down strap weakness or error in properly securing tie-downs). The cylinders contained compressed hydrogen gas at 200 bar (2900 psi). The accident caused some hydrogen cylinders to leak and the associated cylinder package plumbing systems were breached. A spark or other local heat source (e.g., from a nearby vehicle motor) ignited the leaking hydrogen and caused a deflagration/explosion that damaged a car view more
An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.