A five-pound CO2 cylinder being stored in a compressed gas storage cage at a power plant failed catastrophically and became a missile. The cylinder destroyed the storage cage, then struck one of six stationary hydrogen storage cylinders used as emergency make-up for the hydrogen supply system. One of the hydrogen cylinders was broken away from its mounts and moved 10 feet from its original location. The loss of this cylinder severed the manifold tubing, creating a leak path to the atmosphere for the remaining five hydrogen cylinders. The leaking hydrogen gas apparently self-ignited, engulfing the immediate area. The site fire brigade responded and used hose lines from a distance to provide cooling until the hydrogen supply was consumed. The fire was out within seven minutes, and no off view more
An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.
A pressure relief device (PRD) valve failed on a high-pressure storage tube at a hydrogen fueling station, causing the release of approximately 300 kilograms of hydrogen gas. The gas ignited at the exit of the vent pipe and burned for 2-1/2 hours until technicians were permitted by the local fire department to enter the station and stop the flow of gas. During this incident the fire department evacuated nearby businesses and an elementary school, closed adjacent streets, and ordered a high school to shelter in place.
There were no injuries and very little property damage. The corrugated roof on an adjacent canopy over a fueling dispenser was slightly singed by the escaping hydrogen flame, causing less than $300 in damage.
The station's operating systems worked as view more
A fire occurred in a continuous-feed autoclave system (fixed-catalyst-bed tubular reactor) when the rupture disc released, discharging hot oil, oil distillates, and hydrogen gas out a vent pipe into the autoclave cell. The flammable mixture was discharged directly into the cell because there was no system in place to catch or remotely exhaust the autoclave contents. The oil and gas ignited in a fireball that, in turn, ignited nearby combustibles (cardboard and paper), causing a sustained fire. The hydrogen gas and autoclave system were shutoff immediately. However, a lecture bottle containing hydrogen sulfide was heated by the surrounding fire and ultimately ruptured with enough force to cause facility structural damage. (Lecture bottles do not have a pressure-relief device.) The view more
A rupture disc blew on a 20,000-gallon liquid hydrogen tank, causing the vent stack to exhaust cold gaseous hydrogen. Emergency responders were called to the scene. To stabilize the tank, the remaining hydrogen was removed from the tank except for a small volume in the heel of the tank that could not be removed manually. The tank vacuum was lost. Firemen sprayed the tank with water and directed a stream onto the fire exiting the vent stack. The water was channeled directly into the open vent stack, and the exiting residual hydrogen gas (between -423 F and -402 F) caused the water in the vent stack to freeze. The water freezing caused the vent stack to be sealed off, disabling the only exit for the cold hydrogen gas. After a time, the residual hydrogen gas in the tank warmed up, causing view more
- = No Ignition
- = Explosion
- = Fire
- = No Ignition
- = Explosion
- = Fire