A rupture disc blew on a 20,000-gallon liquid hydrogen tank, causing the vent stack to exhaust cold gaseous hydrogen. Emergency responders were called to the scene. To stabilize the tank, the remaining hydrogen was removed from the tank except for a small volume in the heel of the tank that could not be removed manually. The tank vacuum was lost. Firemen sprayed the tank with water and directed a stream onto the fire exiting the vent stack. The water was channeled directly into the open vent stack, and the exiting residual hydrogen gas (between -423 F and -402 F) caused the water in the vent stack to freeze. The water freezing caused the vent stack to be sealed off, disabling the only exit for the cold hydrogen gas. After a time, the residual hydrogen gas in the tank warmed up, causing view more
A partial pressure sensor for an automated gas environment system (AGES) was not functioning correctly for pure hydrogen flow. While personnel were troubleshooting the problem, a burst disk ruptured resulting in a leak of hydrogen gas and actuation of a flammable gas alarm.
System troubleshooting involved the installation of a small hydrogen gas cylinder and temporary manual valve in an engineered ventilated enclosure adjacent to an instrument sample well. A burst disk associated with the temporary manual valve ruptured upon opening of the gas cylinder valve. The vented gas, exhausting through an engineered exhaust system, triggered the flammable gas detector. Personnel promptly evacuated the area in accordance with established procedures. Appropriate personnel responded to the view more