A hydrogenation experiment was being performed under 60 atm hydrogen, inside a high-pressure reactor cell. The experiment was conducted inside a fume hood and left overnight. The hood caught fire during the night, resulting in fire damage to the fixture, hood, and exhaust duct, as well as water damage to much of the building. Based on the local fire department investigation, the fire started from faulty electrical wiring that was used to provide power for reactor cell heating. The electrical fire ignited solvent that was in a dispensing bottle inside the hood, which subsequently overheated the reactor cell, rupturing the seals. The rupture released hydrogen from the cell and attached supply tank, further fueling the fire. Nobody was injured in the incident, and damages were limited. It view more
While attempting to light the hydrogen flare inside a Metalorganic Chemical Vapor Deposition (MOCVD) system burn box, a small explosion occurred, blowing the back section of the burn box off. Hydrogen flow was shut down immediately, and this MOCVD operation was suspended. Researchers made the determination that this was a minor incident and there were no injuries.
The follow-up investigation determined that the MOCVD HEPA filter had become sufficiently loaded to the point where performance of the burn box exhaust ventilation system was significantly degraded. The static pressure created across the "loaded" HEPA filter equaled the operating static pressure of the exhaust ventilation system servicing the burn box. This resulted in a region of "dead air" in the view more