Hydrogen alarms went off in a research laboratory and the fire department was called, but no hydrogen leak was detected. The hydrogen system was leak-checked with helium and found to be leak-free except for a very small leak in the manifold area. The manifold leak was fixed, but because of its small size, it was not thought to be the likely source for the hydrogen alarm trigger. While hydrogen was removed from the system for leak-testing, the hydrogen alarm went off again, and again the fire department responded. There was no hydrogen present in the system to trigger this alarm. Other sources within the building were checked to see what may have set off the alarm, but none were found. One research area uses small amounts of hydrogen, but laboratory logs indicate that none was being view more
Only 25 minutes after the normal work shift ended, an explosion occurred at a hydrogen storage and use facility that had been in a non-operational mode for several months while undergoing modifications for future tests. No one was in the facility at the time of the explosion. The event was viewed about 30 seconds after the explosion by two engineers in a blockhouse 1000 feet away. Authorities were notified and calls were placed to other personnel needed to secure the area. About 8 minutes later, the engineers moved to a vantage point about 450 feet from the facility. There they viewed heat waves rising from a central location on the test pad, heard popping sounds similar to gaseous hydrogen (GH2) venting on a burn pond, and suspected that a hydrogen fire was in process. They returned view more
An explosion occurred at a chemical plant in an analysis room containing various analyzer instruments, including a gas chromatograph supplied with hydrogen. A contract operator was performing work to install a new vent line to a benzene analyzer that was part of a group of CO2 analyzers, but separate and unrelated to the gas chromatograph. During the process of this work, a plant supervisor accompanying the contract operator doing the work had an indication of flammable gas present on a portable detector. This was in conflict with the fixed gas detector in the analysis room that was indicating that no flammable gas was present. As a precaution, the plant supervisor immediately cut off the hydrogen supply and, along with the contract operator, began the normal task of determining if view more
An instrument engineer at a hydrogen production facility was arresting the hydrogen leakage in tapping a pressure transmitter containing 131-bar hydrogen gas. The isolation valve was closed and the fittings near the pressure transmitter were loosened. The pressure dropped from 131 bar to 51 bar. The fitting was further loosened (though very little); the instrument tube slipped out of the ferrule and got pulled out of the fitting. With the sudden release of the 51-bar hydrogen, there was a loud pop (like a fire cracker) and the spark-proof tool was observed to have black spot on it. The volume of the hydrogen gas released was small, since it was in the tapping line only.
Hydrogen leaked from the outlet piping of a hydrogen heating furnace at a fuel oil desulfurization cracking unit during normal refinery operation. The leaking hydrogen caused a localized fire. Dilution water for cleaning polythionic acid collected in the drain nozzle after a turnaround shutdown. The chlorine concentration in this dilution water was high because its concentration in the industrial water was originally high. The chlorine in the industrial water was concentrated by the high temperature, after the plant was restarted, and stress corrosion cracking occurred. Hydrogen leaked and was ignited by static electricity or heat.
A fire occurred at the fuel oil desulfurization cracking unit of a refinery 257 hours after startup of the plant, view more
A bourdon tube ruptured in a pressure gage after 528 hours of operation in a liquid H2 system. The alarm sounded, the system was isolated and then vented.