Two fitting failures were experienced for fueling equipment filling systems. Both fittings were installed in the system thermal chamber experiencing ambient temperatures of -40C to +50C. They were connected in high-pressure lines used for 70MPa hydrogen fueling.
The first fitting, a 0.25-inch NPT hose connection, was in service for approximately one year with no signs of leakage. The failure was noticed when the system was pressurized during a filling sequence. The failure was discovered by an audible hissing noise during leak checking. The system was depressurized and the fitting removed and replaced. The system was re-pressurized with no further leakage.
When attempting to reconnect a second fitting, a double-ferrule high-pressure connection, the fitting in question view more