A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes. Just after the 4136 kPa (600 psig) startup steam was introduced into the reformer furnace inlet, the control room alarm journal reported an extreme positive pressure spike at the same time a single loud bang was reported by the operations view more
Operators in a powdered metals production facility heard a hissing noise near one of the plant furnaces and determined that it was a gas leak in the trench below the furnaces. The trench carried hydrogen, nitrogen, and cooling water runoff pipes as well as a vent pipe for the furnaces.
Maintenance personnel presumed that the leak was nonflammable nitrogen because there had recently been a nitrogen piping leak elsewhere in the plant. Using the plant's overhead crane, they removed some of the heavy trench covers. They determined that the leak was in an area that the crane could not reach, so they brought in a forklift with a chain to remove the trench covers in that area.
Eyewitnesses stated that as the first trench cover was wrenched from its position by the forklift view more