A distillate dewaxing unit at an oil refinery was undergoing hot hydrogen regeneration of the catalyst when an explosion occurred. Catalyst regeneration is a periodically performed procedure, in which the normal liquid hydrocarbon feed is stopped and a hydrogen-rich gas mixture is fed through the catalyst bed for which the normal operating temperature is raised from 700F to 800F. During the catalyst regeneration process the reactor pressure is increased from normal operating levels just below 600 psig to about 640 psig. A pipe failure occurred as a sudden and complete rupture of the 10-inch diameter line at the exit of one of the two reactors. Security video revealed that the release rapidly exapnded and the hot gas mixture ignited shortly after rupture. A shock wave from the resulting view more
A petroleum refinery experienced a catastrophic rupture at one bank of three heat exchangers in a catalytic reformer/naphtha hydrotreater unit because of high temperature hydrogen attack (HTHA). Hydrogen and naphtha at more than 500F were released from the ruptured heat exchanger and ignited, causing an explosion and an intense fire burned for more than three hours.
The rupture fatally injured seven employees working in the immediate vicinity of heat exchanger at the time of the incident. The workers were in the final stages of a start-up activity to put a parallel bank of three heat exchangers back in service following cleaning. Such start-up activities had resulted in frequent leaks and occasional fires in the past and should have been considered as hazardous and nonroutine. view more
A single-stage regulator "failed" while flowing hydrogen gas from a standard 200 cu.ft. gas bottle. The regulator had functioned properly prior to the event through several on-off cycles. During the event, a solenoid valve was opened to allow hydrogen to flow, when a rather loud noise was noted and gas began flowing out of the pressure relief valve on the side of the regulator. It was noted that the low-pressure gauge on the regulator was "pegged" at the high side (>200 psi). The valve on the bottle was shut off, and hydrogen flow was immediately stopped. Hydrogen flowing out of the relief valve did not ignite. With the bottle shut off, the regulator was removed and replaced with another regulator of the same type, and activities continued.
The failed view more
A hydrogen leak at the flange of a 6-inch synthesis turbocharger valve in an ammonia production plant ignited and exploded. Hydrogen detectors and the fire alarm alerted the control room, which immediately shut down the plant, and the fire was then extinguished rapidly. There were no injuries caused by the accident, since the operator heard a wheezing sound and was able to run away just before the explosion occurred. The leaking gas was composed of 70% hydrogen at a flow rate of 15,000 cubic meters per hour. Property damages in the turbocharger included electrical cabling, melted siding, and heavily damaged pipes. The ammonia plant was shut down for more than a month.Five days before the incident, a problem with the CO2 absorber column led operators to open the vent downstream of the view more
Operators in a powdered metals production facility heard a hissing noise near one of the plant furnaces and determined that it was a gas leak in the trench below the furnaces. The trench carried hydrogen, nitrogen, and cooling water runoff pipes as well as a vent pipe for the furnaces.
Maintenance personnel presumed that the leak was nonflammable nitrogen because there had recently been a nitrogen piping leak elsewhere in the plant. Using the plant's overhead crane, they removed some of the heavy trench covers. They determined that the leak was in an area that the crane could not reach, so they brought in a forklift with a chain to remove the trench covers in that area.
Eyewitnesses stated that as the first trench cover was wrenched from its position by the forklift view more
The incident occurred in the catalytic hydrotreatment plant of an oil refinery. The plant, which began operations in September 1997, has a capacity of 1650 tons/day of light fuel oil and 1450 tons/day of heavy fuel oil. The plant was designed to desulfurize the light and heavy fuel oil fractions produced in the refinery by treating them with high-pressure hydrogen over a catalyst to remove sulfur (producing hydrogen sulfide as a byproduct). The plant has two heating/reaction/fractionating sections to treat the two fuel oil fractions, but a single gas purification and compression section for the recycled hydrogen gas.
The heavy fuel oil reactor feedstock from the vacuum distillation plant is sent to the heavy fuel oil treatment section through three pipelines equipped with flow view more
Hydrogen alarms went off in a research laboratory and the fire department was called, but no hydrogen leak was detected. The hydrogen system was leak-checked with helium and found to be leak-free except for a very small leak in the manifold area. The manifold leak was fixed, but because of its small size, it was not thought to be the likely source for the hydrogen alarm trigger. While hydrogen was removed from the system for leak-testing, the hydrogen alarm went off again, and again the fire department responded. There was no hydrogen present in the system to trigger this alarm. Other sources within the building were checked to see what may have set off the alarm, but none were found. One research area uses small amounts of hydrogen, but laboratory logs indicate that none was being view more
Only 25 minutes after the normal work shift ended, an explosion occurred at a hydrogen storage and use facility that had been in a non-operational mode for several months while undergoing modifications for future tests. No one was in the facility at the time of the explosion. The event was viewed about 30 seconds after the explosion by two engineers in a blockhouse 1000 feet away. Authorities were notified and calls were placed to other personnel needed to secure the area. About 8 minutes later, the engineers moved to a vantage point about 450 feet from the facility. There they viewed heat waves rising from a central location on the test pad, heard popping sounds similar to gaseous hydrogen (GH2) venting on a burn pond, and suspected that a hydrogen fire was in process. They returned view more
In the fall of 2007, the operations team began a procedure (a written procedure was being followed) to sample the liquid hydrogen (LH2) storage vessels ("tanks"), and associated transfer system. This procedure was being performed to determine the conditions within the system, and if necessary, to purge the system of any excess gaseous hydrogen (GH2) in preparation for reactivation of the system. The system had not been used since 2003.
The LH2 storage system contains two (2) spherical pressure vessels of 225,000 gallons in volume, with a maximum working pressure (MAWP) of 50 psig. Eight-inch transfer piping connects them to the usage point. Operations began with activation of the burnstack for the LH2 storage area. Pneumatic gaseous nitrogen (GN2) systems in the view more
A steel tube with inner diameter of 6 mm and 10 m length was filled with radiolysis gas (stoichiometric H2-O2 mixture) at 70 bar for boiling water reactor simulations. Via a pneumatic valve, a venting line with similar cross-section and 2 m length, filled with atmospheric air, was connected.
For venting the tube, the valve was opened (fast) and an explosion occurred.
Explanation: Due to diffusion ignition in the leading shock, a flame flashed back into the pre-mixed reservoir and induced a detonation there. The tube system and involved measurement technique was destroyed. For safety reasons, the whole installation was set up in a protective container so that no person or other equipment was threatened.