A leaking liquid hydrogen cryogenic pump shaft during the process of filling a gaseous tube delivery trailer to 2400 psi at a liquid hydrogen transfilling location caused a series of explosions and a fire. After approximately 30 minutes of filling, the operator heard a single loud explosion and then saw flames and ripples from heat generation near the ground in the hydrogen fill area. The operator quickly actuated the emergency alarm system that shut down the cryogenic pump and closed the air-actuated valves on the cryogenic pump supply line. After this shutdown, three smaller explosions were heard as well as the sound of gas releasing from a safety relief valve. The fire department was called to the scene and participated in the final shutdown of the hydrogen system as the fire was view more
Installation of a 9000-gallon liquid hydrogen storage tank by a lessee at a building has not been evaluated for effect on the Safety Authorization Basis (SAB) of nearby facilities.
During review of an Emergency Management Hazard Assessment document, a reviewer questioned whether the SAB of nearby facilities had been reviewed for the effect of the installed 9000-gallon liquid hydrogen tank. Reviews by the facility management and facility safety personnel confirmed the evaluations have not been performed.
The direct cause was determined to be a management problem, with policy not adequately defined, disseminated, or enforced to integrate potential lessee hazards into the facility safety program documentation on the 9000-gallon hydrogen tank and delivery. The existing policy view more