A person working in a hydrogen lab unknowingly closed the wrong hydrogen valve and proceeded to loosen a fitting in one of the hydrogen gas lines. The pressure in the 1/4"-diameter hydrogen line was approximately 110 psig. Hydrogen escaped from the loosened fitting and the pressure release resulted in the tubing completely detaching and falling to the floor. The person noted seeing a white stream around the hydrogen jet leak. The person noted a color change and noise change as the leak ignited (this happened in a matter seconds and he did not have a chance to react). The person left the lab and pushed the emergency stop button. Someone else pulled the fire alarm. Both of these actions were designed to close the main hydrogen solenoid (shutoff) valve. The local emergency response view more
Forty-six hydrogen cylinders were accidentally charged with air instead of additional hydrogen during recharging operations at a synthetic liquid fuels laboratory. Cylinders were manifolded in batches of 10 or 12 to the utility compressor outside the laboratory. In normal operations, partly used cylinders containing hydrogen at a pressure of 800-900 psi were recharged to a pressure of 2000-2100 psi. Since the contaminated cylinders contained a highly explosive mixture of about 40% hydrogen and 60% air, it was decided to release the compressed gas to the atmosphere outside the building after grounding the cylinders. Two of the cylinders were successfully discharged, but an explosion occurred while the third cylinder was being discharged. Two chemical engineers were killed by the blast, view more
A hydrogen reformer furnace at a refinery was shutdown for maintenance to remove and cap the inlet and outlet headers of some radiant tubes that had previously developed hot spots and been isolated by externally pinching them off at the inlet. A decision was made to leave steam in the steam-generating circuit during this maintenance operation to prevent freezing. After maintenance was complete, the startup procedure required the furnace to be first heated up to 350°C (662°F) prior to introducing 4136 kPa (600 psig) steam into the radiant tubes. Just after the 4136 kPa (600 psig) startup steam was introduced into the reformer furnace inlet, the control room alarm journal reported an extreme positive pressure spike at the same time a single loud bang was reported by the operations view more
An explosion occurred in a 90-ton-per-day incinerator at a municipal refuse incineration facility. Three workers were seriously burned by high-temperature gas that spouted from the inspection door, and one of them died 10 days later. The accident happened during inspection and repair of the furnace ash chute damper. The workers injected water to remove some blockage, and the water reacted with incinerated aluminum ash to form hydrogen, which caused the explosion.
Workers noticed that the post-combustion zone was full of ash and the ash pusher was not working properly, so they tried to remove the ash from the inspection door with a shovel. They discovered a solid layer of "clinker", which is formed by solidification of molten material such as aluminum. The explosion view more