The cap on a full cylinder of hydrogen was difficult to remove. A wrench was applied to turn the cap. When the cap was turned, a part of the wrench contacted the valve and opened it. Since the cap was still on the cylinder, the valve could not be closed. The area was evacuated until the cylinder had emptied.
During a refueling event, the operator activated the fueling lever in the wrong sequence. The vehicle filled to proper pressure, but filled faster than normal. Under different circumstances, this could have resulted in overheating of the receiving fuel tank.
While a hot air dryer was being used to free a coupling in a hydrogen cryostat (an apparatus used to maintain constant low temperatures), a flash fire occurred. The H2 cryostat was being dismantled.
The temperature at the center of the cryostat was sufficiently low to liquefy air. The prescribed requirements for purging and bringing the cryostat to room temperature were circumvented. The H2 - air mixture was formed and ignition was assumed to be a spark from an open filament of the dryer.
One morning a saltwell pump was placed in operation. Operation of this equipment requires that the Standard Hydrogen Monitoring System (SHMS) cabinet be in operation. Later that morning, during the morning surveillance rounds, the Standard Hydrogen Monitoring System (SHMS) cabinet was found not to be in the operational mode.
On the previous day, the night shift saltwell operator assigned to run the saltwell pump had placed the SHMS monitor in operational mode; however, the saltwell system was not started at this time. Shift turnover was conducted and the condition of the SHMS was turned over to the appropriate saltwell operator and shift manager. During the day shift the day shift operator assigned to the complex received approval from the operations engineer to place the SHMS view more
An unplanned shutdown of the hydrogen supply system occurred, affecting the hydrogen furnaces in the plant. The apparent cause was an inadvertent valve closing, which was contrary to the written procedure.
A preventative maintenance activity was being conducted on the hydrogen gas system. Shortly after starting that work, various hydrogen gas users notified the emergency response personnel that the hydrogen supply safety alarms sounded, indicating an interruption of the hydrogen gas supply. As a result, the hydrogen furnaces shut down. This shut down is an automated process which injects an inert gas (nitrogen or argon) to prevent the introduction of oxygen and its mixing with any hydrogen gas. All shut downs functioned as designed. As a precautionary measure, fire protection view more
A demolition technician noted an elevated combustible gas lower explosive limit (LEL) on a pipe that was being tested prior to cutting (No. 2 pipe). The No. 2 pipe was one of four pipes being tested. The other three pipes tested less than detectable for combustible hydrogen gas. Testing involves tapping the pipe and connecting the pipe to an Explosive Gas Detector via a tube. When an elevated LEL is identified, the pipe is allowed to vent and then retested prior to cutting. After tapping the No. 2 pipe, the work crew left the pipe open to vent and departed the area for the end of shift.
At approximately 7"45 PM on the same day, a crew was on overtime to support roofing activities. Since additional workers were available, the craft supervisor decided to re-enter the viewing view more
An employee noticed an unusual smell in a fuel cell laboratory. A shunt inside experimental equipment overheated and caused insulation on conductors to burn. Flames were approximately one inch high and very localized. The employee de-energized equipment and blew out the flames. No combustible material was in the vicinity of the experiment. The fire was contained within the fuel cell and resulted in no damage to equipment.
The employee was conducting work with a fuel cell supplied by oxygen gas. The hazard control plan (HCP) associated with the work was for use with fuel cells supplied by air or hydrogen, but not for oxygen, which yields a higher current density. The technician had set up the station wiring to handle a current of 100 amps and the shunt was configured to handle a view more