Overview: A hydrogen leak and explosion occurred due to the installation of an incorrectly sized gasket at the suction line of a hydrogen compressor in a refinery hydrodesulfurization plant. The incorrectly sized gasket was mounted during the startup of the plant in 2001 and had never being inspected nor replaced.
Incident synopsis: The operating conditions were stable when the operator received an alarm indicating pressure loss in the circuit. He immediately instructed his field personnel to inspect the area. The hydrogen leak was confined inside the compressor room because the walls and roof were not provided with ventilation devices. An explosion occurred, causing two fatalities and the destruction of the compressor room and some of the surrounding area.