A person working in a hydrogen lab unknowingly closed the wrong hydrogen valve and proceeded to loosen a fitting in one of the hydrogen gas lines. The pressure in the 1/4"-diameter hydrogen line was approximately 110 psig. Hydrogen escaped from the loosened fitting and the pressure release resulted in the tubing completely detaching and falling to the floor. The person noted seeing a white stream around the hydrogen jet leak. The person noted a color change and noise change as the leak ignited (this happened in a matter seconds and he did not have a chance to react). The person left the lab and pushed the emergency stop button. Someone else pulled the fire alarm. Both of these actions were designed to close the main hydrogen solenoid (shutoff) valve. The local emergency response view more
The interior of a small high-temperature furnace, approximately 24 inches high by 18 inches wide, became contaminated with an unknown material later identified as magnesium. The furnace was disassembled to clean the unknown material from the interior surfaces, and while attempting to clean the bottom of the furnace, the technician tapped the upper lip of the furnace with a spatula and the magnesium flashed. The technician was stepping back from the furnace when the magnesium flashed. He received minor eye irritation and his eyebrows were singed.
Later that week the same technician was attempting to clean the interior surfaces of the top of the furnace and sprayed, as directed, the interior of the top with a water-based cleaning liquid which consisted of 91% water. He stepped view more
An individual inadvertently connected a pure hydrogen gas bottle to a chamber/glove box as opposed to a 10% hydrogen (in nitrogen) bottle that should have been used. [The wrong bottle had mistakenly been delivered, and the inexperienced individual did not know the difference.] The hydrogen concentration increased within the chamber to about 9%. Since there was insufficient oxygen in the chamber to support combustion, the hydrogen did not burn, and was quickly diluted with nitrogen.
A H2 delivery truck accident occurred on a highway. The truck was pulling a trailer containing gaseous H2. Upon entering a sharp curve, the truck and trailer started to weave and pushed to the side of the road. The truck and trailer rolled about 40 feet downhill; the trailer rolled over 1 1/2 times and the tractor once, ending in the upright position with the driver still in his seat. The truck was completely totaled, but little damage was incurred by the trailer. The trailer shell was satisfactory with normal venting through the stack. The rear cabinet doors were warped shut.
The accident occurred on a bad road, which was steep with many sharp curves. The driver was going too fast for the road conditions and the type of trailer being view more
A fatal accident took place at an onshore processing facility for slop water from the offshore petroleum industry.
Drilling fluids, or mud, are typically oil-water emulsions consisting of base oil (continuous phase), water (dispersed phase), and emulsifying agents. Used drilling mud, or slop, is mud enriched with water and rock cuttings from drilling --- typically 60-80% water, 10-20% emulated base oil, and 10-20% rock cuttings. The used drilling fluids are collected in slop tanks on oil platforms and later shipped to onshore facilities for further processing.
On the day of the accident, two operators were trying to remove the lid from a manhole on top of a 1600-cubic meter storage tank. However, they were not able to unscrew the rusted bolts holding the lid in place, and view more
Two scientists were changing hydrogen gas cylinders in an analytical laboratory. They were in the process of removing the cylinder cap from the new cylinder when a loud hissing noise occurred and they quickly realized that the tank was leaking. After making a quick attempt to shut off the tank, which was not possible, they left the lab and notified their supervisor.
After checking that everyone was out of the lab, the supervisor paged all staff in the vicinity to immediately evacuate to the staging area. Facility management and ES&H management were notified about the situation, and they contacted the local fire department to respond to the site in case the venting gas was ignited.
The first responders arrived quickly and spoke with facility management and the site view more
A refinery hydrocracker effluent pipe section ruptured and released a mixture of gases, including hydrogen, which instantly ignited on contact with the air, causing an explosion and a fire. Excessive high temperature, likely in excess of 1400°F (760°C), initiated in one of the reactor beds spread to adjacent beds and raised the temperature and pressure of the effluent piping to the point where it failed. An operator who was checking a field temperature panel at the base of the reactor and trying to diagnose the high-temperature problem was killed. A total of 46 other plant personnel were injured and 13 of these were taken to local hospitals, treated, and released. There were no reported injuries to the public.
Property damage included an 18-inch (46-centimeter) long tear in the view more
An explosion occurred in a 90-ton-per-day incinerator at a municipal refuse incineration facility. Three workers were seriously burned by high-temperature gas that spouted from the inspection door, and one of them died 10 days later. The accident happened during inspection and repair of the furnace ash chute damper. The workers injected water to remove some blockage, and the water reacted with incinerated aluminum ash to form hydrogen, which caused the explosion.
Workers noticed that the post-combustion zone was full of ash and the ash pusher was not working properly, so they tried to remove the ash from the inspection door with a shovel. They discovered a solid layer of "clinker", which is formed by solidification of molten material such as aluminum. The explosion view more
A hydrogen explosion occurred in a university biochemistry laboratory. Four persons were taken to the hospital for injuries. Three of these were treated and released shortly thereafter; the fourth was kept overnight and released the following evening. All of the exterior windows in the laboratory were blown out and there was significant damage within the laboratory. One sprinkler was activated that controlled a fire associated with a compressed hydrogen gas cylinder.
First responders from the local community and the university campus were quickly on the scene. Once the injured were attended to and the site secured, response efforts focused first on assessing potential hazards (electrical, fire, hazardous materials, etc). Campus personnel worked into the night to board up windows view more