A person working in a hydrogen lab unknowingly closed the wrong hydrogen valve and proceeded to loosen a fitting in one of the hydrogen gas lines. The pressure in the 1/4"-diameter hydrogen line was approximately 110 psig. Hydrogen escaped from the loosened fitting and the pressure release resulted in the tubing completely detaching and falling to the floor. The person noted seeing a white stream around the hydrogen jet leak. The person noted a color change and noise change as the leak ignited (this happened in a matter seconds and he did not have a chance to react). The person left the lab and pushed the emergency stop button. Someone else pulled the fire alarm. Both of these actions were designed to close the main hydrogen solenoid (shutoff) valve. The local emergency response view more
The interior of a small high-temperature furnace, approximately 24 inches high by 18 inches wide, became contaminated with an unknown material later identified as magnesium. The furnace was disassembled to clean the unknown material from the interior surfaces, and while attempting to clean the bottom of the furnace, the technician tapped the upper lip of the furnace with a spatula and the magnesium flashed. The technician was stepping back from the furnace when the magnesium flashed. He received minor eye irritation and his eyebrows were singed.
Later that week the same technician was attempting to clean the interior surfaces of the top of the furnace and sprayed, as directed, the interior of the top with a water-based cleaning liquid which consisted of 91% water. He stepped view more
An apprentice mechanic lacerated his right forearm while quickly sliding out from under a hydrogen prototype bus when the bus slipped off a hydraulic jack. The apprentice and another mechanic had raised the bus about 1 foot from the ground to position it on jack stands when the hydraulic jack tipped over. The apprentice went to the site medical facility, where he needed five stitches to close the wound in his forearm.
The mechanics were raising the rear of a hydrogen prototype bus, like the one in the figure below, and placing it on jack stands. After chocking the wheels, they used bottle jacks on each side of the rear axle to raise the bus high enough to place a 20-ton hydraulic jack under the differential. With the bus resting on a pair of small jack stands, they raised the view more
A technician was welding a cable suspended over a stainless steel H2 instrument line. During the welding process, two holes were accidentally burned through the hydrogen tubing. The operator heard a hissing sound and closed the valve, but the hydrogen had already ignited and it burned his hand while he was feeling for a leak.
A short during welding caused the pinholes in the tubing containing the gaseous H2.
A refinery hydrocracker effluent pipe section ruptured and released a mixture of gases, including hydrogen, which instantly ignited on contact with the air, causing an explosion and a fire. Excessive high temperature, likely in excess of 1400°F (760°C), initiated in one of the reactor beds spread to adjacent beds and raised the temperature and pressure of the effluent piping to the point where it failed. An operator who was checking a field temperature panel at the base of the reactor and trying to diagnose the high-temperature problem was killed. A total of 46 other plant personnel were injured and 13 of these were taken to local hospitals, treated, and released. There were no reported injuries to the public.
Property damage included an 18-inch (46-centimeter) long tear in the view more
A hydrogen explosion occurred in a university biochemistry laboratory. Four persons were taken to the hospital for injuries. Three of these were treated and released shortly thereafter; the fourth was kept overnight and released the following evening. All of the exterior windows in the laboratory were blown out and there was significant damage within the laboratory. One sprinkler was activated that controlled a fire associated with a compressed hydrogen gas cylinder.
First responders from the local community and the university campus were quickly on the scene. Once the injured were attended to and the site secured, response efforts focused first on assessing potential hazards (electrical, fire, hazardous materials, etc). Campus personnel worked into the night to board up windows view more